How to Repair a Water Heater and Oven Circuit Feedback Condition
Electrical Circuits Question: Hi Dave, I recently went from a gas range to an electric wall oven. It is a Maytag 3.6kW@240V that I bought used.
Water Heater and Oven Circuit with a Voltage Feedback Condition
Water Heater and Oven Circuit with Voltage Feedback Conditions
Hi Dave, I recently went from a gas range to an electric wall oven. It is a Maytag 3.6kW@240V that I bought used.
It is on a segregated circuit with #12 copper wire, 3 wire installation, with a 20A breaker. It has operated for several months without problem until a few days ago, when the breaker tripped while preheating the oven. I reset it and it immediately tripped again.
The panel is in the basement, and I noticed that the water heater had just kicked on because of the noise it makes when first starting. The water heater has 2 3800W elements also on a segregated circuit with 10/2 wire with a 30A breaker.
It has never had any problems other than scale and lower element burnout. When I shut off the water heater, the oven worked just fine. Can you think of a reason these appliances on separate circuits would effect each other?
Hi Steve - Great Question.
I am assuming that both the oven and water heater are on dedicated 240 volt circuits, each being served by their own 2-pole circuit breakers. If this is true - then I would shut off the circuit breaker and look for a loose connection or burnt wire, possibly where the wiring connects to the heating elements. Sometimes the controls will wear out as well, but make sure that all of the connections are ok. If the wiring and connections look ok, then I would check the circuit breaker and make sure that there is a reading of 240 volts between the two terminals. If this reading is not correct then there is a possibility that the breaker is bad or has a connection problem with the buss of the panel. All of these connection checks should be made with the circuit power OFF.
The process of elimination is the best way to troubleshoot starting with the most vulnerable parts of the electrical device. A check of the connection where the oven power is being supplied at the junction or splice would be good to check as well.
Let me know what you find out.
From: Steven N
Dave, I haven't tested it yet, but It seems you hit the nail square on the head. The wire from the lower heating element was loose at the water heater thermostat. It probably loosened the last time I changed out the element. I appreciate your help very much,. if you have time, could you explain to me why this would impact the oven circuit?
Combined conversation between Steve and Dave:
1 - Are you saying that even though an obvious problem was identified, I may still have a problem which needs to be corrected?
Possibly, however it is hard for me to tell from here. As stated initially - these two circuits should operate independently of each other under normal conditions. If you were to remove the loose wire from the water heater, insulating it with electrical tape to keep it safe, and try to duplicate what occurred before, then yes - you may in fact have another problem which sounds like a feed-back. If you find that you cannot duplicate the problem with the oven buy performing this test then it was just a coincidence. If the original problem occurs again while the water heater is wired correctly then it is possible that there is a problem with the oven wiring.
2 - Is it possible that the loose water heater wire was the only source of the problem?
If you wish, perform the test as mentioned above and see what happens.
If the original condition repeats itself then there is an additional problem. I would be surprised if there is a feed-back occurring because typically a feed-back would affect other circuits as well, but bit all depends on what is really occurring and where with respect to the all the electrical circuits.
I would be interested to know if your service is fed from a main panel of a sub-panel. Please understand that it is difficult for me to troubleshoot from my remote position, so I am offering suggestions based upon my experience and typical conditions which are commonly found.
Hi Steve -
The water heater and oven circuit should not affect each other at all, with one exception. If there is a problem with the main breaker or sub-main breaker that feeds the panel which supplies power to these two circuits then there will most likely be what is known as a feed-back.
A feed-back commonly occurs through other 240 volt large appliances especially when they are off there by creating a path for electricity to feed back through the heating elements of the 240 volt large appliance.
Here is a typical Voltage Feed Back scenario:
A main breaker has a bad connection on one of the 240 volt incoming legs of main power. Because the panel has circuits feeding from two legs of 120 volts each, the circuits being fed from the defective side can actually pull power through a 240 volt appliance. In most cases, the voltage will be around 94 volts due to the 240 volt appliance having a heating element which acts as a resistor which allows the power from the working side of the service to back feed the deficient side of the service.
This condition can cause a lot of potential problems within the service and the electrical components being fed. A condition such as this needs to be identified and corrected asap. The above scenario may in fact be happening with your service, and this happens more during the hot summer months due to expansion and contraction of electrical connections and heavy electrical loads being placed on large circuits.
This condition can be identified by an electrician who would measure the incoming voltages and the voltages of each circuit leaving the panel, then measuring the voltage at each dedicated circuit and branch circuit. When an abnormal or low voltage reading is identified then the process would be to examine the circuit back to the panel or source until then problem is discovered.
The problem could be a loose or burnt splice or connection or possibly a burnt or faulty breaker. Some times it is something as simple as a 240 volt breaker that has one side tripped in the off position, even when it appears to be in the on position. Every once and a while the problem may be identified on the electrical utility primary side of the service which would then require the attention of the electrical utility company.
I hope this helps you.
You Can Avoid Costly Mistakes!
Here is How to Do It:
Wire It Right with the help of my Illustrated Wiring Book
Great for any Home Wiring Project.
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
How to Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.
Electrical Tips to Help You Wire it Right
The Safest Way to Test Electrical Devices and Identify Electric Wires!
The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!
The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets
Light indicates if wiring is incorrect
Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!
The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
More about Water heater and oven circuit feedback conditionsSitemap
Ceiling Fans Airplane Ceiling Fan Airplane Ceiling Fan Ceiling Fan Direction Summer Ceiling Fan Direction Winter Ceiling Fan Wiring Diagram 1 Ceiling Fan Wiring Diagram 2 Ceiling Fan Wiring Questions and Answers Ceiling Fans Wiring – Part 1 Ceiling Fans Wiring – Part 2 Introduction to Ceiling Fan Remote Controls Outdoor Ceiling Fan 1 Outdoor […]
water heater and oven circuit feedback conditions - 373