How to Wire a 220 Volt Heater Circuit to Sub Panel
Electrical Circuits Question: I'm having a problem with wiring a 220 volt heater circuit. I installed a 20 amp double pole breaker in my panel, and I ran 12/2 wire with a ground to the outlet.
Check Out What Others Are Sharing at Ask the Electrician: It's awesome! Michael from Sonora, California
Installing and Connecting a 220 Volt Heater Circuit to a Sub Panel
I'm having a problem with wiring a 220 volt heater circuit.
I installed a 20 amp double pole breaker in my panel, and I ran 12/2 wire with a ground to the outlet. On the breaker, I connected the white and black wires to each pole, and connected the bare copper wire to ground.
At the outlet, I connected the bare copper wire to ground (the green terminal), and I connected the white wire to one side, and the black wire to the other.
When testing with a volt meter, if I put one terminal on ground and one terminal on either pole, I get 110 volts.
If I put both terminals on the poles, I get nothing. Aren't I supposed to be getting 220? The bottom line is that the 220 volt heater that I bought isn't working when I plug it in. The heater is single phase, so I didn't think it mattered which side I connected the black and white wires to. Regardless, the heater still doesn't work if I reverse them. At first, I thought the heater might be defective, so I exchanged it for another one, but the new one doesn't work either. Obviously, there's something wrong with the way I wired the outlet. Can you help? Thanks- Patrick D.
Hi Patrick - Great Electrical Repair Question!
It sounds like the two breakers are attached to the same buss, so your only getting the 110 volt reading. This can happen if you are using a Twin Breaker. If this is the case then you need to use a full size 2-pole breaker. If you are using a full size 2-pole breaker then for some reason your panel is not getting both hot legs. You need to check this and let me know what you find. Check anywhere in the panel across two hot legs to see if you get a 220 volt reading.
If you don't get a 220 volt reading you'll have to find out what feeds the panel you are at and see if it is wired right or there may be another problem. We wont get into that right now, lets just take it one step at a time and check the panel where the heater circuit originates from. From: Patrick D. Ok, we're on the right track. I'm wiring to a sub panel that's in my garage and I've attached a picture of it. If I take my volt meter and connect it to the red and black supply wires, I'm getting 220 volts
If you look at that 20 amp double pole breaker on the right, that's what I'm wiring my outlet to. If I touch the volt meter leads to each pole of the breaker, I get nothing. One lead to a pole and one lead to ground, I get 110 on each pole. From: Patrick D. Ok, I killed the power to this sub panel before I started messing around in it. When I bought this double pole breaker to do this little project, I noticed that it only had one metal clip at the bottom, but the whole box of breakers where I bought it were like this, so I didn't think much of it. Is this normal? I've attached a picture of the panel with the breaker out as well as a picture of the back of the breaker.
Hi Patrick, I looked at the pictures closer and I think I see the black wire loop up and then down into the right hand lug - so if this is the case it is ok. Then from the looks of this panel you may only be able to have one 2-pole breaker that actually gives 220 volts and I'll bet that it will be the center two spaces. You would know this by pulling out the two center breakers and see that the busses are separated. So in this case what you need to do is careful pull the 2-pole breaker and reinstall it to the center area of the panel. After you do this you will have the 220 volts necessary for your heater circuit.
Be sure to turn off the power before you do this!
From: Patrick D.
You da man!
Attached is a picture of the panel with all the breakers out. I put the double pole breaker right there in that middle spot, and viola! It works!
Thanks for all your help.
Electrical Wiring Video #2
Electrical Wiring Tips for Home Electrical Wiring Projects
Tripping Circuit Breaker, Outlet at a Wall Switch, Light Fixture without a Ground Wire, Help with Home Electrical Wiring Projects.
See more House Wiring Videos from Ask The Electrician:
Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electric Circuits 120 Volt and 240 Volt Outlet Circuits Wiring Light Switches Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring NEC Codes for Home Electrical Wiring ....and much more.
Electrical Wiring for an Attached Garage How to Plan the Electrical Circuits for Your Garage - Garage electrical wiring diagram and considerations for wiring garage circuits, complete with pictures. Careful planning for your garage with immediate and future equipment considerations will help you understand how to size your electrical circuit requirements.
Installing a Dryer Circuit and Breaker How a Quad Electrical Circuit Breaker Could Be Used - In this case, the 2-pole may be replaced by a quad 30 amp circuit breaker which will provide the 240 volt circuit for the electric dryer. The circuit wiring configuration is critical and must be done correctly in order for both of the circuits to work correctly, and of course, the quad circuit breaker must be available for that particular make and model electrical panel.
Electrical Panel Size Considerations What size should the Main Electric Service Panel be for all the Electrical Circuits? How to Determine What Size an Electrical Panel Should Be, Factors that must be considered when sizing an electrical panel.
Intermediate to Advanced - Electrical Repairs and Circuit Wiring is Best Performed by a Licensed Electrical Contractor.
Basic Electricians Pouch of Hand Tools, a Voltage Tester and a Multi Meter.
Depends on personal level experience, ability to work with tools, work with electrical wiring, and the available access to the project area. Precaution:
Identify the project circuit, turn it OFF and Tag it with a Note before working with the wiring.
Modifying existing electrical circuits or installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
This is a testing tool that is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
This is great to troubleshoot a problem with outlet circuit wiring, is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect, Very handy and easy to use.
A wire stripping tool used to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets.
» How To Wire It RIGHT!« Wire it with Confidence! Fully Illustrated Instant Download Now You Can Wire it like a Pro!
I think your site offers the the clearest and best electrical information for homeowners I have ever seen on the net.You have given me confidence to do my own projects which I never had before. THANK YOU! Paul, from Foxboro, Massachusetts
I wish I found this site earlier, it is by far the best electrical related resource I have found on the web. George, from Scranton, Pennsylvania
I love this site for an office worker that does not know anything about electric wiring. Bill, from New York City, New York
This site is so much better than the 3 books I just bought, I wish I came here first. Collin, from Grand Rapids, Michigan
Thank you for answering my question.
I was able to get this done. This site is perfect. I am glad I found it. Please keep it going. Mike, from Chicago, Illinois