Electrical Circuits Question: I have a 200A main panel which is fully utilized. I recently put in an in ground swimming pool and a finished basement - so I put in a main lug 20 circuit 100A panel downstream to service my pool and basement.
Swimming Pool Electrical Circuit
Electrical Circuits Question:
I have a 200A main panel which is fully utilized. I recently put in an in ground swimming pool and a finished basement - so I put in a main lug 20 circuit 100A panel downstream to service my pool and basement.
Everything went all right until recently my 200A main breaker occasionally trips . This happened tonight when both central air units were on, (one -4 ton unit one 2 ton unit) my pool pump 15A and my washing machine.
I went to the main panel and measured 19A off one leg and 45 off the other. I may try load balancing and move the 4 ton unit to the leg drawing 19A - but I can't understand why this would trip a 200A main?
Hi Mike - Great Electrical Repair Question! Mike - keep in mind that the starting amps of any motor is quite high. This is commonly called Lock Rotor Amps LRA and will be found on the A/C Unit Label Information. If both A/C units start at the same time and there is a moderate load in the home you may trip your main breaker. So how can you solve this? One option is to have a Time Delay Relay installed on one of the A/C units as to prevent both units from starting at the same time. The relay can be installed on the thermostat control voltage side of the circuit. You mentioned that you may try to balance the load of the A/C units, however they are most likely 240 Volts and should themselves be balanced. You can balance the panel loads by repositioning the higher 120 Volt loads onto the low reading buss. Let me know how it works out.
Thanks for your quick response on this holiday weekend - you are correct both AC units are running on 240V and by default are load balanced - its been a long week. The LRA on the 4 ton unit is 105 and the LRA on the 2 ton unit is 55. The 4 ton units's compressor outside shows a min fuse rating of 29A and a max of 50A - I was surprised to see that the 30A breaker that the 4 ton unit is on has never tripped. I thought I may have needed a new 200A main or maybe the terminals on it were loose. I guess if both units fire at the same time and my pool pump, well and other appliances are on at the same time I will have a potential problem. As for the time delay relay what manufacturer/rating would you recommend? I will also look at moving some of the higher 120V circuits, but the time delay relay sounds like a real fix.
»You Can Avoid Costly Mistakes!«
Here is How to Do It:
Wire It Right with the help of my Illustrated Wiring Book Great for any Home Wiring Project.
Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electric Circuits 120 Volt and 240 Volt Outlet Circuits Wiring Light Switches Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring NEC Codes for Home Electrical Wiring ....and much more.
Intermediate to Advanced - Electrical Repairs and Circuit Wiring is Best Performed by a Licensed Electrical Contractor.
Basic Electricians Pouch of Hand Tools, a Voltage Tester and a Multi Meter.
Depends on personal level experience, ability to work with tools, work with electrical wiring, and the available access to the project area. Precaution:
Identify the project circuit, turn it OFF and Tag it with a Note before working with the wiring.
Modifying existing electrical circuits or installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
I think your site offers the the clearest and best electrical information for homeowners I have ever seen on the net.You have given me confidence to do my own projects which I never had before. THANK YOU! Paul, from Foxboro, Massachusetts
I wish I found this site earlier, it is by far the best electrical related resource I have found on the web. George, from Scranton, Pennsylvania
I love this site for an office worker that does not know anything about electric wiring. Bill, from New York City, New York
This site is so much better than the 3 books I just bought, I wish I came here first. Collin, from Grand Rapids, Michigan
Thank you for answering my question.
I was able to get this done. This site is perfect. I am glad I found it. Please keep it going. Mike, from Chicago, Illinois