How to Wire a Swimming Pool Circuit

 Summary: Electrical Circuits Question: I have a 200A main panel which is fully utilized. I recently put in an in ground swimming pool and a finished basement - so I put in a main lug 20 circuit 100A panel downstream to service my pool and basement.

Check Out What Others Are Sharing at Ask the Electrician:
It is clear, concise and easy to understand. John from Warren, Ohio

How to Install and Wire a Sub Panel

Will Display at the End of This Video

Electrical Circuits Question:

I have a 200A main panel which is fully utilized. I recently put in an in ground swimming pool and a finished basement - so I put in a main lug 20 circuit 100A panel downstream to service my pool and basement.

Everything went all right until recently my 200A main breaker occasionally trips . This happened tonight when both central air units were on, (one -4 ton unit one 2 ton unit) my pool pump 15A and my washing machine.

I went to the main panel and measured 19A off one leg and 45 off the other. I may try load balancing and move the 4 ton unit to the leg drawing 19A - but I can't understand why this would trip a 200A main?
Mike.

 Hi Mike - Great Electrical Repair Question! Mike - keep in mind that the starting amps of any motor is quite high. This is commonly called Lock Rotor Amps LRA and will be found on the A/C Unit Label Information. If both A/C units start at the same time and there is a moderate load in the home you may trip your main breaker. So how can you solve this? One option is to have a Time Delay Relay installed on one of the A/C units as to prevent both units from starting at the same time. The relay can be installed on the thermostat control voltage side of the circuit. You mentioned that you may try to balance the load of the A/C units, however they are most likely 240 Volts and should themselves be balanced. You can balance the panel loads by repositioning the higher 120 Volt loads onto the low reading buss. Let me know how it works out. Dave Thanks for your quick response on this holiday weekend - you are correct both AC units are running on 240V and by default are load balanced - its been a long week. The LRA on the 4 ton unit is 105 and the LRA on the 2 ton unit is 55. The 4 ton units's compressor outside shows a min fuse rating of 29A and a max of 50A - I was surprised to see that the 30A breaker that the 4 ton unit is on has never tripped. I thought I may have needed a new 200A main or maybe the terminals on it were loose. I guess if both units fire at the same time and my pool pump, well and other appliances are on at the same time I will have a potential problem. As for the time delay relay what manufacturer/rating would you recommend? I will also look at moving some of the higher 120V circuits, but the time delay relay sounds like a real fix. Thank you!

Home Electrical Wiring

Helping You Wire it Right

NOTE: A List of All my Helpful Videos
Will Display at the End of This Video

 » You Can Avoid Costly Mistakes! « Here is How to Do It: Wire It Right with the help of my Illustrated Wiring Book Great for any Home Wiring Project.

Complete Guide to Home Electrical Wiring

Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Includes:
Wiring GFCI Outlets
Wiring Home Electric Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring Light Switches
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
How to Troubleshoot and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
NEC Codes for Home Electrical Wiring
....and much more.

The Safest Way to Test Electrical Devices and Identify Electric Wires!

The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.

The Quickest Way to Check for Faulty Electrical Wiring!

The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.

Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!

The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..

The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.

RELATED

Electrical Code and Swimming Pool Light Fixtures
GFCI Ground Fault Protection for Swimming Pool Lights: NEC Article 680-20, As described in this electrical question, anyone who enters the pool with this light on is in Danger of Potential Electrical Shock!

Testing 220 Volts
Testing 220 Volt Electrical Circuit Wiring: On a 220 volt circuit I am getting 120 between green and black and green and the red wire, is this correct?

Question – 200 Amp Main Circuit Breaker Tripping – Part 1
My 200 amp main electrical circuit breaker trips. Should I replace it?

May is National Electrical Safety Month
During National Electrical Safety Month in May, Dave at Ask The Electrician is encouraging homeowners to eliminate electrical safety hazards in and around their home. Electrical hazards can result in property damage, potential injuries and even deadly electrocutions.

Electrical Question about a Dangerous Pool Area Circuit
I see no mention of any GFCI protection for the pool area and equipment, and if now you are experiencing a possible voltage leak this creates an extremely dangerous condition for any one in the area of the swimming pool...