I bought a front load washer/dryer and because of the doors swings, placement is opposite from original layout.
I have relocated the dryer vent and now I want to relocate the rcpt. The dryer cord can reach the old receptacle location but the washer hose hook up is directly in front of the receptacle.
Can I add or splice to the existing cable and use the old rcpt box as a junction box?
Thanks- John P.
Hi John - Great Electrical Repair Question! Yes - you can use the existing receptacle box as a splice box to extend the circuit to a better location. Here are the steps to follow: Be sure to turn off the circuit, mark it so no one turns it back on and verify it is off at the receptacle. Pay careful attention to how the receptacle is wired, which wire goes where, especially the ground (and neutral if there is one). Use the exact same wire size and type to extend the circuit. The wiring should be run inside the walls, but if you need to extend the circuit on the surface of the walls then you need to install the wiring without the romex style jacket or purchase individual wires of the same gage and install them in conduit using connectors attached to a metal extension box on the existing box, then to a new surface mounted receptacle box in the new location. Support conduit with straps and firmly mount the new box preferably where a stud is so you can use wood screws.
Junction the extended wires with good wire connectors sized properly for the wire gage. Be sure to cover the original box with a blank cover. plastic or metal. Make up the receptacle in the new box and replace the cover. Turn the circuit on and test it out.
Let me know if this helps.
From: John P.
Thanks for replying to my question, but the more I thought about it the more I didn't like splicing. In addition, the existing cable is a 10-3 with no ground wire. Saw were the codes now require 10-3 with ground wire. Even though my existing cable met the code since my house was built in 1989, I thought what the heck, I'll go ahead and run a new cable to the box and get things up to code. Had all the studs exposed already since I put in a new 4 vent line to vent outside. My dryer room is located in the middle hallway with no exterior wall. Anyhow, installation is complete and all is working well. Thanks, John.
Electrical Wiring Video #2
Electrical Wiring Tips for Home Electrical Wiring Projects
Tripping Circuit Breaker, Outlet at a Wall Switch, Light Fixture without a Ground Wire, Help with Home Electrical Wiring Projects.
See more House Wiring Videos from Ask The Electrician:
Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electric Circuits 120 Volt and 240 Volt Outlet Circuits Wiring Light Switches Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring NEC Codes for Home Electrical Wiring ....and much more.
How to Install Wiring for a Stack Washer and Dryer Guidelines to Provide Power for a Stack Washer and Dryer: Many stack washer dryer units are actually two separate units, each having its own specific electrical circuit requirement depending on the exact models that are purchased.
The Importance of Electrical Circuit Polarity How to Identify and Repair Reverse Polarity of an Electrical Circuit: Electrical Safety and Proper Circuit Polarity, Polarity has to do with the flow of electricity. Polarity and Outlets, Circuit Wires and Polarity.
The Importance of Electrical Cover Plates Prevent Electrical Hazards by Covering Switches and Outlets - One great safety measure is to simply replace an switch or outlet cover to avoid the exposure of electrical wiring and to keep fingers from coming into contact with energized parts.
Intermediate to Advanced - Electrical Repairs and Circuit Wiring is Best Performed by a Licensed Electrical Contractor.
Basic Electricians Pouch of Hand Tools, a Voltage Tester and a Multi Meter.
Depends on personal level experience, ability to work with tools, work with electrical wiring, and the available access to the project area. Precaution:
Identify the project circuit, turn it OFF and Tag it with a Note before working with the wiring.
Modifying existing electrical circuits or installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
This is a testing tool that is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
This is great to troubleshoot a problem with outlet circuit wiring, is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect, Very handy and easy to use.
A wire stripping tool used to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets.
» How To Wire It RIGHT!« Wire it with Confidence! Fully Illustrated Instant Download Now You Can Wire it like a Pro!
I think your site offers the the clearest and best electrical information for homeowners I have ever seen on the net.You have given me confidence to do my own projects which I never had before. THANK YOU! Paul, from Foxboro, Massachusetts
I wish I found this site earlier, it is by far the best electrical related resource I have found on the web. George, from Scranton, Pennsylvania
I love this site for an office worker that does not know anything about electric wiring. Bill, from New York City, New York
This site is so much better than the 3 books I just bought, I wish I came here first. Collin, from Grand Rapids, Michigan
Thank you for answering my question.
I was able to get this done. This site is perfect. I am glad I found it. Please keep it going. Mike, from Chicago, Illinois