More about Electrical Junction Boxes
Recent Questions and Comments
Checking Light Fixture Wiring Connections
I am adding more light fixtures, the new lights do not work, but the original light does work, what did I do wrong? Common Problems with Light Fixtures and Dimmer Switches and How to Fix Them.Read more...
What To Do With The Ground Wire
Where do I attach the ground wire? Grounding Wall Outlets and Light Switches: What to do When there is Nothing to Attach the Ground Wire, Grounding Wall Outlets and Light Switches, Ground Wires and Ungrounded Fixtures and Boxes, Bonding the Ground Wire.Read more...
Electric Water Heater Wiring
How are the wires connected to a water heater? Common Wiring Methods for an Electric Water Heater, Basic Water Heater Circuit Requirements, Connect Water Heater Wiring.Read more...
Ceiling Fan Wiring Diagram Black White Red and Green Wires
How to Connect the Black White Red and Green Wires of a Ceiling Fan: Connecting the white, black, blue and green wires.Read more...
» Guide to Home Wiring
» Ask an Electrical Question
Electrical Wiring Junction Boxes
By Dave Rongey
Summary: Understanding electrical junction boxes and what they are used for. Home electrical wiring is the process of installing electrical wire to a location that will serve electrical devices or an appliance.
Electrical Junction Boxes, Fixture Boxes, Receptacle Boxes, Splice Boxes
One very important component is the box where the wire will be installed. The type and size of the home wiring electrical boxes will depend upon the circuit size, application and its location.
Box Fill - How many wires you can put in a box? The NEC Code requires wiring to be protected and enclosed when devices such as receptacles, fixtures and switches are being installed. Sometimes it is necessary to junction or splice wires in home wiring electrical boxes.
When splicing wires, an accessible electrical junction box box is necessary to enclose the spliced wires, thus the trade name is electrical enclosure.
This list shows various electrical boxes and displays the box name and describes the typical application.
The most common type of materials that home wiring electrical boxes are made of are: plastic, fiberglass, steel, aluminum and bakealight. The metal boxes come with knock-outs for using conduit such as EMT (electrical metallic tubing) or flex- steel or aluminum.
Why don't you see the exact same electrical box at your supplier? The availability of the types of boxes will depend upon which electrical manufacturer or purchasing channel your supplier has a contract with.
Boxes and Wire-Fill
How many wires can be installed into an electrical box will depend on how many Cubic Inches the box has and what size wires are being installed.
Below is a chart of a few common home wiring electrical boxes and the actual information which should be stamped or molded into each enclosure.
A good rule of thumb is to never over fill a box, leave yourself plenty of room, and don't cut your wire too short either - you can always trim off a little, but you can't stretch it. Keep in mind that the Ground Wires are not counted.
|ELECTRICAL BOX EXAMPLES||
|3-INCH PANCAKE METAL||4.5||2||2||0|
|3-INCH CUT-IN FIBERGLASS||14.0||7||6||5|
|1-GANG CUT-IN FIBERGLASS||16.0||8||7||6|
|1-GANG CUT-IN FIBERGLASS||18.0||9||8||7|
|1-GANG NAIL PLASTIC||20.5||10||9||8|
|2-GANG CUT-IN FIBERGLASS||28.0||14||12||11|
|2-GLASS FACE NAIL PLASTIC||32.0||16||14||12|
|3-GANG CUT-IN FIBERGLASS||42.5||21||18||17|
|2-GANG NAIL PLASTIC||43.5||21||19||17|
More about Electrical Box Fill Calculations
Common Home Electrical Wiring Boxes and How to Use Them
|Electrical Box||Part Name||Electrical Applications|
|1-Gang Plastic Nail Box used for Type NM Cable wiring. Also known as a Rough-In Box.||Outlets and Switches.|
|1-Gang Fiberglass Cut-In Box with a Back Bracket.||Outlets and Switches. Type NM Cable wiring. Used with cable wiring in Remodel applications.|
|1-Gang Metal Cut-In Box with Adjusting Mounting Ears.||Outlets and Switches, with knock-outs for steel or aluminum flex.|
|1-Gang Handy Box.||Outlets and Switches. Surface mount Microwave Receptacle. Garage or Shop area with Conduit.|
2-Gang Plastic Nail Box.
|Outlets and Switches.|
|2-Gang Fiberglass Cut-In Box.||Outlets and Switches.|
|2-Gang Plastic Face Nail Box.||Outlets and Switches. Great for tight areas with limited room to nail.|
|3-Gang Plastic Side Nail Box.||Outlets and Switches.|
|3-Gang Face Nail Box.||Outlets and Switches.|
|3-Gang Fiberglass Cut-In Box.||Outlets and Switches.|
|4-Gang Plastic Nail Box.||Switches and Lighting Controls.|
|3-Inch Fiberglass Nail Box.||Lighting Fixtures and Junctions.|
|3-Inch Fiberglass Cut-In or Remodel Box.||Lighting Fixtures and Smoke Detectors.|
|3-Inch Metal Pancake Box, also available in Fiberglass.||Lighting Fixtures. Mounted on the surface of the framing to be flush with finished sheet rock.|
|4-Inch Plastic Nail Box.||Lighting Fixtures|
|4-Inch Ceiling Fan Box.||Ceiling Fan Pancake Box, approved for 70 Lb Support.|
|4-Square Metal Box. Use with raised rings for 1 or 2 Gangs, 3-0 or 4-0 openings.||Receptacles and Switches. Surface mount for use in Garage or Shop area with EMT or Flex Conduit.|
|Top of Page|