Electrical Circuits Question: I am hooking up a tanning bed. According to the instructions, It operates from a 220 AC source.
Check Out What Others Are Sharing at Ask the Electrician: This is really cool. A place where I could ask a question and hopefully get an answer to rather than the puzzled look I got at Home Depot. Adam from Sun city center, Florida
I am hooking up a tanning bed. According to the instructions, It operates from a 220 AC source. It requires a 6-20R outlet and a dedicated 20 amp circuit.
I have ran the 12/2 with ground wire. I've installed the outlet. That leaves the breaker. From my somewhat limited knowledge, I assumed I need a 2 pole 20 amp breaker. The panel is a Zinsco.
I was able to find the breakers online and purchased a R38-20 (2 X 1Pole 20Amp 120/240V breaker). The R series matches the other skinny breakers already being used. Inside the panel I connected the bare copper wire to the ground bar and the white and black to the breaker.
After hooking everything up and turning on the tanning bed, one side of the breaker trips after about 10 seconds. I am starting to wonder if the breaker is wrong. I am thinking its not an actual 2 pole breaker, but a twin single pole. this would make a difference, Right? Thanks- Tim N.
Hi Tim - Great Electrical Repair Question!
The Zinsco R38-20 breaker should provide 240 volts if the connections on the bottom of the breaker are staggered where they will come into connection with the opposite busses in the panel. This means that one side of the twin breaker will connect to one of the busses of the panel and the other will side of the breaker will connect with the other buss of the panel which would produce 240 volts. It's always best to check the voltage source at the breaker before attaching the wires to make sure of your voltage. This can be done with a tester capable of reading 240 Volts AC and connecting the two leads to the terminal screws on the breaker. It is always a good idea to check terminal to terminal which should produce 240 volts, and then each terminal to ground to verify 120 volts. Once the voltage is verified make sure the wires are inside the terminals all the way. The Twin Zinsco breakers have a very small area to insert the wire and it can be tricky to get the wire all the way inside the terminal.
Let me know what you find.
From: Tim N.
Dave, The breaker does have the staggered contacts and I have the connections all the way in the terminals. So I cant figure why its not working I did ask the person who sold it to me and his email response was JUST PUT IN THE SAME THING (WIRE ETC .)BUT WITH THE TWO POLES!
What else do you think it could be? Thanks
Hi Tim - If you are providing the specified power to the tanning bed and the circuit is tripping then there may be a problem internally with the tanning bed. To find out what it is would involve a process of elimination, such as disconnecting one component at a time. However if the unit is brand new you may be voiding your warrantee. In that case I would contact the provider and ask for a replacement or some type of resolution. Because the circuit is not tripping immediately this would not indicate a direct short, so I believe there may be a component that is not right. With most tanning beds there aren't very many components, mainly the lights, fan and timer, but there may be a problem with one of these components. Have you made a voltage check to ground and terminal to terminal? From: Tim N. No I have not checked the volts. I am away from the panel, so I can't at this time. I will and report back to you. It may be awhile as its a project I am doing for my girl friend out of state. She lives in a condo and the the breaker box looks pretty standard to me. She did have an electrician look at it before I got involved to make sure that the service would handle the added circuit and he said it would. I have added circuits before without any issue in my house and thought i could handle this.
Thanks for the follow-ups.
Electrical Wiring Video #2
Electrical Wiring Tips for Home Electrical Wiring Projects
Tripping Circuit Breaker, Outlet at a Wall Switch, Light Fixture without a Ground Wire, Help with Home Electrical Wiring Projects.
See more House Wiring Videos from Ask The Electrician:
Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electric Circuits 120 Volt and 240 Volt Outlet Circuits Wiring Light Switches Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring NEC Codes for Home Electrical Wiring ....and much more.
Tanning Bed Circuit Requirements Installing the Right Circuit When Wiring a Tanning Bed: How to Plan and Installing a Tanning Bed Circuit - The electrical specifications need to be identified on the tanning bed label to see if the required circuit has been installed.
Electrical Circuit for a Tanning Bed How to Provide Electrical Power for a Tanning Bed: The Most Common Electrical Circuit Requirements for Installing Tanning Bed, Tanning Bed Circuit Types, Installing a Tanning Bed Circuit
How to Install Wiring in a Basement Can the Romex brand wire be used when Wiring a Basement? Romex or metal cable: What should be used when wiring a basement and how is the wiring protected. NEC Code Article Sections 336-6c, 333-11
Intermediate to Advanced - Electrical Repairs and Circuit Wiring is Best Performed by a Licensed Electrical Contractor.
Basic Electricians Pouch of Hand Tools, a Voltage Tester and a Multi Meter.
Depends on personal level experience, ability to work with tools, work with electrical wiring, and the available access to the project area. Precaution:
Identify the project circuit, turn it OFF and Tag it with a Note before working with the wiring.
Modifying existing electrical circuits or installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
This is a testing tool that is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
This is great to troubleshoot a problem with outlet circuit wiring, is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect, Very handy and easy to use.
A wire stripping tool used to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets.
» How To Wire It RIGHT!« Wire it with Confidence! Fully Illustrated Instant Download Now You Can Wire it like a Pro!
I think your site offers the the clearest and best electrical information for homeowners I have ever seen on the net.You have given me confidence to do my own projects which I never had before. THANK YOU! Paul, from Foxboro, Massachusetts
I wish I found this site earlier, it is by far the best electrical related resource I have found on the web. George, from Scranton, Pennsylvania
I love this site for an office worker that does not know anything about electric wiring. Bill, from New York City, New York
This site is so much better than the 3 books I just bought, I wish I came here first. Collin, from Grand Rapids, Michigan
Thank you for answering my question.
I was able to get this done. This site is perfect. I am glad I found it. Please keep it going. Mike, from Chicago, Illinois