Learn Electrical Wiring Home Electrical Wiring Book Home Electrical Wiring Home Electrical Course Basic Home Electrical Wiring Course Online FREE Electrical eBook and Newsletter Electrical Mistakes and How to Avoid Them

# New Range Electrical Outlet

 Summary: Electrical Outlet Question: Electrical outlet for new range 220 line. I am renovating an old house, including a complete kitchen remodel. © By: Dave Rongey

## Wire a Range Cord and Outlet

### So Keep Watching So I Can Help You Wire it Right!

Electrical Outlets Question:
Electrical outlet for new range 220 line
I am renovating an old house, including a complete kitchen remodel. I removed the old electric-only wall oven, which was wired directly (no outlet) to a 220 line coming up through the floor underneath it.

I need to move the line over a few feet to where the new gas/electric range will be.

The installation manual for the new range says the following:
We recommend that the range be installed with a power cord set (not supplied). The electrical rating of the power cord set must be 120/240 volt, 30 amperes minimum.

Range Power Cord
The power cord set shall be marked for Use with Ranges.
Always use a new power cord. Ranges are dual rated for use on either 120/240 VAC or 120/208 VAC. Most wiring codes require a separate circuit with separate disconnect switch and fuses either in the main entrance panel or in a separate switch and fuse box.

The range requires a minimum of a three wire 120/240 or 120/208 volt, 30 AMP, 60 Hz AC circuit.
I know I'll need to install an outlet, which I'm presuming will need to be a 220 outlet (since it's a 220 line). So my naive question is this- what is the difference between \ 220\ and \ 240 VAC\ ? Same thing for \ 110\ vs \ 120 VAC\ ?

I'm thinking these are one and the same in what they reference?

Given that the manual says for use on either 120/240 VAC or 120/208 VAC, I should be able to use my existing 220 line, since I have confirmed it is on its own circuit, right?

Tim

Hi Tim - Great Electrical Repair Question!
Yes you are right, 110/120 and 220/240 volt are meaning the same things. There are countries where the voltage is more specific, and we do have some commercial services which will actually produce 208 volts, but that is getting into areas outside of the home.

Range Circuit
Yes, you can use your existing range circuit as long as the extended wiring is placed in an accessible junction box, and if you extend the circuit with anything other than the original wire gauge then you will need to replace the circuit breaker to protect the smallest gauge wire on the circuit.

I strongly advise extending with the original wire gauge because it maintains the integrity of the circuit.

## A Complete Guide to Home Electrical Wiring

Be sure to get your copy of my BIG Book:
Perfect for Homeowners, Students and Electricians
Includes:
Home Electrical Wiring - Room by Room
120 Volt Circuits
240 Volt Circuits
Multi-Wired Circuits
Wiring Methods for Installing Home Electrical Circuit Wiring
Electrical Codes for Home Electrical Wiring
....and much more.

### RELATED

Replacing a Standard Wall Outlet
How to Wire a Wall Outlet - Example of Outlet Wiring when there are more than one cable from the electrical circuit.

Remodeling a Bathroom with GFI Outlet and Lights
How is a bathroom wired with GFCI outlets and light fixtures? Electrical Wiring for a Bathroom Remodel Project.

Repair a Tripping GFCI Outlet
GFI and GFCI Questions: The GFCI Does Not Always Trip, Lost Power to Other Plugs and Light, The GFI to my Bathroom Quit Working. How to Fix Common Problems with GFCI Outlets, Guide to Troubleshoot and Repair a GFCI Outlet Problem.

Wire 220 Volt Receptacle Outlets
How should I install two 220 Volt Receptacles that Require Two Individual Power Sources? Options for Installing Two 220 Volt Receptacles that Require Two Individual Power Sources.

Wire a Switched Outlet to Control a Lamp
Wire a Switched Outlet for a Lamp | Identify the Electrical Circuit Wiring, Switched Outlet Wiring Diagram.

Wiring a Light Fixture to a GFCI Outlet
I added a spot light to an outside receptacle, checked for voltage before closing up box, now the light does not work, could it be the GFCI receptacle?

Fix a Tripping GFCI Outlet for a Freezer or Refrigerator
My freezer lost power, do I have a bad GFCI receptacle? Problems with GFCI Outlets for Freezers and How to Fix Them.

Wiring a GFCI Outlet with No Ground Wire Video
How is a GFCI outlet wired for a 2-wire circuit that does not have a ground wire? Wiring a GFCI Outlet on a 2-Wire Circuit.

outlet - 1456