By Dave Rongey Summary:
Electrical Outlets Question:
Our kitchen has 4 outlets each 2nd outlet has stopped working. I've checked for power with a voltage tester.
Check Out What Others Are Sharing at Ask the Electrician: I think it is great that someone is willing to help others like this. We need more people like this in this World. Phil from Dumaguete city, UK
Electrical Outlets Question: Our kitchen has 4 outlets each 2nd outlet has stopped working.
I've checked for power with a voltage tester.
There is power in the wall leading to the outlet, yet no power on the actual wire. I believe that all 4 outlets are all connected to one circuit, so why would every 2nd outlet be dead?
I changed each outlet, yet there's no power indicated going to the wire, on each of the 3 wire's red, one or black.
Hi Neil - Great Electrical Repair Question! Check GFCI Outlets
Have you checked to see if any GFI outlets or breakers are tripped? Electrical Codes require that kitchen outlets be protected by GFI receptacles or breakers.
Once you discover the source of the GFI's I would double check to make sure they are wired correctly, Hot in to Line, and Load for the outlets downstream.
As you described the wire colors you may have a 3-wire circuit where the neutral is shared with two circuits, red and black, or there may be another wiring method installed which could only be discovered with a voltage tester.
Also when something like this happens, ask yourself what has happened recently which may have caused this to happen?
Have all of these outlets worked fin in the past?
I realize these a simple questions, however many times very obvious things happen which may be overlooked that become a knee-slapping moment when you realize the cause.
Electrical Wiring Video #2
Electrical Wiring Tips for Home Electrical Wiring Projects
Tripping Circuit Breaker, Outlet at a Wall Switch, Light Fixture without a Ground Wire, Help with Home Electrical Wiring Projects.
See more House Wiring Videos from Ask The Electrician:
Perfect for Homeowners, Students, Handyman, Handywomen, and Electricians Includes: Wiring GFCI Outlets Wiring Home Electric Circuits 120 Volt and 240 Volt Outlet Circuits Wiring Light Switches Wiring 3-Wire and 4-Wire Electric Range Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet How to Troubleshoot and Repair Electrical Wiring Wiring Methods for Upgrading Electrical Wiring NEC Codes for Home Electrical Wiring ....and much more.
How to wire a range for 3-wire and 4-wire cords I wired my 3 wire 40amp electric range and the electric burners turn on, but the control panel does not work. Wire and 4-Wire Cord Connections for an Electric Range or Freestanding Stove, Connecting the Ground Wire, and Installing a New Circuit for an Electric Range.
220 240 Volt Air Compressor Wiring How to Wire a 220 Volt Air Compressor and Control Switch: Wiring a standard 240 volt motor for equipment such as an air compressor there are only two insulated wires for the 220/240 volts and one separate wire for the ground.
Receptacles Not Getting Full Power Why Do I Only Have 70 Volts on a 120 Volt Receptacle? How to Troubleshoot and Repair Outlet Problems, The Most Common Problem with Electric Outlets and How to Repair Them.
Range Circuit Wiring and 3-Wire Outlets How to Connect the Wires for a Electric Range Cord: Electric Range Installation with a typical 220 or 240 Volt electric power cord wiring system, You may find yourself with either a 3-wire or 4-wire electric range cord.
How to Wire a Range Hood Exhaust Fan Installing Wiring for a Range Hood Exhaust Fan: Wiring from an Existing Power Source or Outlet, I am wiring a hood exhaust fan over the kitchen range cook top.
Intermediate to Advanced - Electrical Repairs and Circuit Wiring is Best Performed by a Licensed Electrical Contractor.
Basic Electricians Pouch of Hand Tools, a Voltage Tester and a Multi Meter.
Depends on personal level experience, ability to work with tools, work with electrical wiring, and the available access to the project area. Precaution:
Identify the project circuit, turn it OFF and Tag it with a Note before working with the wiring.
Modifying existing electrical circuits or installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
This is a testing tool that is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
This is great to troubleshoot a problem with outlet circuit wiring, is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets
Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency
Lights indicate if wiring is correct and indicator light chart is included
Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect, Very handy and easy to use.
A wire stripping tool used to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets.
» How To Wire It RIGHT!« Wire it with Confidence! Fully Illustrated Instant Download Now You Can Wire it like a Pro!
I think your site offers the the clearest and best electrical information for homeowners I have ever seen on the net.You have given me confidence to do my own projects which I never had before. THANK YOU! Paul, from Foxboro, Massachusetts
I wish I found this site earlier, it is by far the best electrical related resource I have found on the web. George, from Scranton, Pennsylvania
I love this site for an office worker that does not know anything about electric wiring. Bill, from New York City, New York
This site is so much better than the 3 books I just bought, I wish I came here first. Collin, from Grand Rapids, Michigan
Thank you for answering my question.
I was able to get this done. This site is perfect. I am glad I found it. Please keep it going. Mike, from Chicago, Illinois