» Residential Electrical Wiring: Guide to Home Wiring
» Need Electrical Help? Get a Quick Reply! Ask the Electrician
Kitchen Outlets Not Working
By Dave Rongey
Why Some Kitchen Outlets are Not Working
Electrical Outlets Question:
Our kitchen has 4 outlets each 2nd outlet has stopped working.
I've checked for power with a voltage tester. There is power in the wall leading to the outlet, yet no power on the actual wire. I believe that all 4 outlets are all connected to one circuit, so why would every 2nd outlet be dead?
I changed each outlet, yet there's no power indicated going to the wire, on each of the 3 wire's red, one or black.
Hi Neil - Great Electrical Repair Question!
Check GFCI Outlets
Have you checked to see if any GFI outlets or breakers are tripped? Electrical Codes require that kitchen outlets be protected by GFI receptacles or breakers.
Once you discover the source of the GFI's I would double check to make sure they are wired correctly, Hot in to Line, and Load for the outlets downstream.
As you described the wire colors you may have a 3-wire circuit where the neutral is shared with two circuits, red and black, or there may be another wiring method installed which could only be discovered with a voltage tester.
Also when something like this happens, ask yourself what has happened recently which may have caused this to happen?
Have all of these outlets worked fin in the past?
I realize these a simple questions, however many times very obvious things happen which may be overlooked that become a knee-slapping moment when you realize the cause.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.