How to Locate a Voltage Problem
Why is the electrical circuit voltage not reading normal with a voltage tester? How to Locate a Voltage Problem, Electrical Tests for Locating the Cause of Incorrect Voltage.
Guide to Locating a Voltage or Power Problem
Electrical Question: Why is the electrical circuit voltage not reading normal with a voltage tester?
- I was moving an outlet today to widen a doorway and after doing the work I checked to make sure everything was working good with a cheap multimeter.
- I was a bit shocked when it started registering about 140volts.
- The breaker hadn’t tripped but I shut it off thinking something wasn’t right. I went over everything and it all looked OK and the same as before.
- I turned the breaker back on and it was still reading 140volt.
- I checked other circuits in the house and got the same voltage.
- I started thinking the multimeter was fried, but after trying it at another site and getting the expected steady 115volts there I came back here and it is still reading about 130volts initially and then slowly (about 1volt/second) climbs to about 140volt.
- Am I being paranoid or is this too far out of parameters?
I’ve lived here for about 40 years and never really noticed an issue beyond some AM radio that had interference that I thought was coming from the power lines along the road, and there’s an insulator on one pole that in a heavy fog a while back seemed to be sparking.
- I wish I’d put a multimeter in a plug earlier to know if it has always been this way, but I never had a reason to.
- I’m not even sure why I checked the voltage this time, except that it was handy and the circuit I moved had a 14/3 line running a hot carrier down the line and I wanted to be sure nothing was over voltage (220volt) when I was done, if that makes sense.
Thanks in advance for any advice or guidance, and please ask if you need more info.
This electrical wiring question came from Dan, in Canada, Canada.
Thanks for your electrical wiring question Dan.
How to Check for the Cause of Incorrect Voltage
Application: Evaluating Incorrect Voltage of a Home Electric Circuit.
Skill Level: Advanced – Not Recommended for Homeowners or DIY’ers – Best performed by an Experienced Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester and amp meter or load recorder.
Estimated Time: Depends on the type and age of the electric service panel and the access to the circuits to be evaluated.
Caution: Working in an electric panel is dangerous due to arc flash hazards and the possibility of electric shock.
Notice: Making changes to the Home Electrical Service Panel should be done according to local and national electrical codes with a permit and be inspected.
Testing Procedure to Locate a Voltage Problem
IMPORTANT: Voltage Testing inside an electrical panel is not recommended for anyone who is not an experienced electrician. The following is an example of the various testing procedure a qualified electrician may use to help locate a problem with incorrect electric circuit voltage.
- Incorrect Voltage on Electrical Circuits
Call the electric utility provider and have them come out and check the voltage on their side of the electrical service, and be sure to tell them about any associated anomalies.
- There are instances when a transformer is failing, or another problem may be occurring on the utility line in the area.
- The Process of Testing the Voltage at the Main Electrical Panel
CAUTION: Do not access the wiring cabinet where the utility company wiring is located within the main electrical panel, or any other section of the electric panel where there are seals or devices to discourage access. These areas are off limits and should only be accessed by an authorized technician of the electric utility company.
- Main Power Voltage Test
CAUTION: Main Breakers are still energized on the LINE SIDE of the main supply of the electrical utility power even while the circuit breaker is in the OFF or OPEN position. Turning OFF a circuit breaker disconnects circuit power only to the LOAD SIDE.
At the main panel inside the circuit breaker section, turn off all of the circuit breakers, including the main breaker and test the voltage on the incoming power on the primary side of the main circuit breaker, or test the secondary side of the main breaker with the main breaker on if necessary.
- Incorrect Voltage
If the voltage reading is incorrect then call the utility company to recheck the primary circuit and transformer.
- Correct Voltage
If the voltage is correct then begin turning on each circuit breaker one at a time and continue measuring the voltage.
- This testing process is intended to identify a circuit that is causing a problem with the voltage.
- When the circuit is identified note the circuit number and the equipment or device(s) that are being supplied.
Working With the Problem Electrical Circuit
- Problem with Circuit Equipment
If the problem circuit supplies power to equipment such as an air conditioner then the AC unit will need to be checked by a HVAC service technician.
- Problem with a Shared Circuit
If the circuit is a shared with multiple outlets or light fixtures then begin the process of removing or disconnecting all of the devices until the problem has been located.
- Circuit Component Problem
If a shared circuit is the problem even when all of the devices have been disconnected, then portions of the the circuit cable wiring will need to be identified, disconnected and tested, one section at a time until the problem is located and repaired.
More about Troubleshooting Electrical Circuit Voltage Problems
Troubleshooting and Repairing Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Understanding Digital Volt Meters
When working on home electrical wiring using voltage meter can play an important part in electrical safety. Electrical testers and voltage meters enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.
Types of Electrical Testers
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Home Electrical Safety
Home Electrical Safety Articles
Electrical Safety Articles covering several topics of home electrical safety and Do-It-Yourself Electrical Safety.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical, Power Quality, Testers and Meters, Using Electrical Testers and Meters, Volt Readings and Home Electrical Wiring:|
|« Previous||Next »|
|How to Wire a Double Switch or Triple Switch||Sizing A Main Electrical Panel For A Home|