» Residential Electrical Wiring: Guide to Home Wiring
» Need Electrical Help? Ask the Electrician
Installing a Occupancy Sensor Switch for a Bath Exhaust Fan
How is a Occupancy Sensor wired to control a bathroom exhaust fan? Wiring a Motion Occupancy Switch: Wiring Diagram for a Motion Detector Occupancy Switch.
How to Wire a Motion Occupancy Switch for a Bath Exhaust Fan
[ad#block]Electrical Question: How is a Occupancy Sensor wired to control a bathroom exhaust fan?
I have bought a small extractor fan or exhaust fan which I want to install in my bathroom.I want to make it go on only when people enter the room so I bought a motion occupancy sensor. Can you please explain how I should wire them.
Background: Emmanuel, a Handyman in the UK.
Additional Comments: A very useful site. Keep up the good work!
Thanks for your electrical wiring question Emmanuel.
Wiring a Motion Occupancy Switch
Application: Wiring a Motion Occupancy Sensor Switch.
Skill Level: Beginner to Intermediate – Best performed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with hand tools.
Precaution: Identify the light circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
Materials: Make sure the occupancy sensor has the same amperage and voltage rating for the electrical load, and is fully compatible with the electrical circuit and the device it will be controlling.
Installing a Occupancy Sensor Switch in a Bathroom
- The occupancy sensor or switch is typically installed in the switch box on the wall.
- The wiring is straight forward except that some of these occupancy sensor switches require a neutral wire for the 120 volt applications.
- The electrical wiring would be connected with the power source in and load out to the bathroom exhaust fan, a neutral wire if required and a ground wire.
- Below is one example of a occupancy motion sensor switch wiring diagram which should be helpful.
- Please read the complete installation instructions for your specific motion occupancy sensor switch for your bathroom exhaust fan.
Wiring Diagram for a Motion Detector Occupancy Switch
More about Wiring a Occupancy Switch
For more information about Bath Exhaust Fan
Bath Exhaust Fan
Bathroom Exhaust Fan
Answers to all of your questions about installing a bath exhaust fan and your bathroom exhaust fan replacement project.
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
|More articles about Electrical, Occupancy Sensor Switch and Home Electrical Wiring:|
|« Previous||Next »|
|Circuit Wiring for a Sub-Panel||Wiring Connections When Replacing a Light Fixture|
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.