How to Install Generator Power for Your Home
How to Connect a Generator Transfer Switch to the Home Panel: Connecting the Generator to the Home.
Wiring a Generator Transfer Switch to the Home Panel
Electrical Question: I would like an electrical drawing of a residential Generator rated at 120/240 volt, 30 amp.
- The generator has a total running power of 7,200 watt’s.
- I will use flex cable between the generator and 120/240 volt. 30 amp receptacle rated for out side use.
- The out side receptacle will be fed into the garage where the inside sub panel will be located.
- It will be able to fit four 15 Amp single phase breakers rated at 120 Volt.
- The sub panel will be a 120/240 volt 30 amp with the main power supply is about eight inches away.
- The main power supply is a 120/240 volt, 200amp panel with a main circuit breaker.
- The chosen circuits to be transferred, their neutrals and ground wires are feed into a separate conduit from the main power supply to the sub panel.
- Wiring the Generator Circuits
- Is a special main circuit breaker for the main power supply panel required for the back up designated circuits?
- Or are these designated back up circuits placed in the same screw slot where the original breaker is? Is this not a code violation.
Thank you for the memory refresher. It’s been a long time. From an old I.B.E.W. retired wire man.
This electrical question came from: Ed, from St. James, New York.
Thanks for your electrical wiring question Ed.
Connecting Generator Power to the Home Electrical System
Application: Installing a Generator
Skill Level: Intermediate to Advanced – Best installed by a Licensed Electrical Contractor, Not Recommended for Homeowners.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for installing the generator and transfer switch.
Estimated Time: Depends on the type and size of the generator and transfer switch and the available access to the project area.
Precaution: Any existing electrical wiring within the immediate area that may interfere with the installation of the transfer switch may need to be relocated if necessary. Special consideration must be given to the existing electric service panel and the circuits that will be powered by the generator.
Important: Installing a generator and transfer switch must be well thought out and performed with a permit with all work being inspected.
Options for Connecting Generator Power
When integrating a generator power source to a home one concern is to provide separation between the generator power and the electric utility power to prevent damage to equipment and eliminate the possibility of sending power from the generator onto the electric company utility lines where a line man may be working.
- The Home Electrical Panel
- The method to accomplish the separation of power will depend on the existing panel that is at the home and the number of circuits which will be powered with power from the generator.
- Connecting the Generator to the Home The most typical options include:
- A main power transfer switch.
- A generator circuit panel.
- Circuit Breaker Interlock kit or device.
- The Cost for Installing a Generator
- The cost for each of these options will depend on the amount of power or the amperage provided by the generator and the number of circuits that will be on generator power, and the type of transfer switch or generator panel that is installed.
More about Home Generators
Home Electric Generators
This series covers a wide variety of topics all about home generators including sizing, selecting, connecting and safely operating this all important addition to your home.
The Importance of a Generator Transfer Switch
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Electrical Code Articles for Home Wiring
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical-grounding, electrical-project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, and smoke-detectors.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Basement GFCI Electrical Wiring||How to Improve Ceiling Fan Lighting »|