» Home » Electrical Wiring Projects
» Residential Electrical Wiring: Dave's Guide to Home Wiring
Grounds and Neutrals in Electrical Panel
How to Wire Grounds and Neutrals in Sub Panels – all the neutrals and ground wire and terminal bars must be separated from each other, and your sub feed should be a 4-wire cable that has a separated insulated neutral wire and a separate ground wire.
Separation of Grounds and Neutrals in Sub Panels
[ad#block]Electrical Question: I have a new Siemens 100 amp panel. I removed the neutral tie bar, how do I properly bond this panel?
- I will be using the left side of the panel for my ground bar since I removed the tie bar.
- Should the left side be bonded?
This electrical wiring question came from: Steve, a Homeowner from Arlington Hts ,IL
Thanks for your electrical wiring question Steve.
How to Wire Grounds and Neutrals in Sub Panels
Skill Level: Advanced – Licensed Electrical Contractor, Not Recommended for Homeowners.
Tools Required: Electricians Pouch of Hand Tools.
Estimated Time: Depends on the extent of the project, the grounding method to be used and available access to the project area.
Precaution: This is an extensive project that should be performed by a Licensed Electrical Contractor.
Notice: Making changes to the Electrical Service Panel should be done with a permit and be inspected.
- Because of the size of the panel I’m assuming this is a sub panel, and yes, all the neutrals and ground wire and terminal bars must be separated from each other, and your sub feed should be a 4-wire cable that has a separated insulated neutral wire and a separate ground wire.
- You should see a copper bonding strap that is screwed to the panel enclosure.
- Just loosen the screw and move this strap so that it is placed into a terminal and tighten it up.
- This will be the bonded ground terminal.
- The other terminal will be for the neutrals.
- These two terminal strips should now be isolated from each other.
- The only place where these two can be bonded is back at the main panel, except for modular or mobile homes.
More about Grounds and Neutrals in Sub Panels
House Wiring Circuits and Circuit Breakers
|Summary: Electrical Sub-Panel wiring considerations for the home complete with pictures. Careful planning for your Sub-Panel with immediate and future load considerations will help you understand how to size your Sub-Panel. This information will help as you consider a Sub-Panel and its size.|
The following may also be helpful for you:
Electrical Wiring Video #2
Home Electrical Wiring Videos about this Topic and More
Dave's Companion Guide to Home Electrical Wiring:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical Wiring, Grounding, Grounding Panels and Home Electrical Wiring:|
|« Previous||Next »|
|How to Test Electrical Circuits for a Home Generator||Replacing a Light Fixture With a Ceiling Fan|