Electrical Code and Swimming Pool Light Fixtures
GFCI Ground Fault Protection for Swimming Pool Lights: NEC Article 680-20, As described in this electrical question, anyone who enters the pool with this light on is in Danger of Potential Electrical Shock!
Swimming Pool Light Fixtures
Electrical Question: We have a pool with a 120 volt light. Should the light be on a GFCI circuit?
- We have an in ground pool with a pool light with 120 volts. It is an incandescent bulb, not LED. Does the national electrical code require this pool light to be on a GFCI breaker/circuit?Our pool pump/light is on a 220 line. I ask this question because it WAS on a GFCI and a bad rainstorm tripped it and an electrician came out and said that is your problem, it is on a GFCI and they “fluctuate” too much. He then installed a regular breaker non GFCI for our pool.
- I have done some research and found out that this can cause a dangerous situation, possible electrocution of people in the pool if something happens.
- So that is my question. Does a 120 volt pool light on a 220 line need to be GFCI protected? Because if it does, then this electrician that the pool company hired does not know what he is doing and could have caused our pool pump to burn up, spark a fire or electrocuted someone in our pool.
Thanks for your electrical question Lara.
Background: Lara, a Homeowner from La Porte, Texas.
Application: Swimming Pool Lights.
Skill Level: Beginner to Intermediate – best performed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools.
Precaution: Identify the circuit, turn it OFF and Tag it with a Note before working with the wiring.
Notice: Installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
GFCI Ground Fault Protection for Swimming Pool Lights
Pool Light Fixtures Require a GFCI Ground Fault Circuit
WARNING: If you have a pool light that is not protected by GFCI Ground Fault Circuit protection then the occupants in or around the swimming pool are at grave risk of potential electrical shock, this includes pets and other animals as well!
VERY IMPORTANT: PLEASE – Turn OFF the circuit to your swimming pool light or electrical outlets that are NOT GFCI Protected, call a Qualified Licensed Electrician and have the necessary Ground Fault Protection installed.
As described in this electrical question, anyone who enters the pool with this light on is in Danger of Potential Electrical Shock!
National Electrical Code: NEC Article 680-20 Pool Light Fixture
- The National Electrical Code – Article 680-20a1 states that a pool light fixture over 15 volts must be GFCI Protected.
- The very reason the original GFCI circuit breaker tripped indicates that there is something wrong with the circuit, and the GFCI circuit breaker was providing the protection against a potential electric shock.
- The alleged “electrician” who removed this GFCI protection has placed himself in an extremely liable position.
- This person should be notified and asked to come back and place the GFCI circuit breaker back on the circuit, then I would hire a Qualified Licensed Electrician who knows more about the electrical code.
- I would also notify the pool company who uses this other person and inform them of their inadequacies and the liable position their actions are placing onto the referring pool company.
- You have also stated that the 120 volt light is fed from a 220 volt pump circuit. If this is the case then this needs to be changed because a 220 volt pump circuit does not provide the necessary isolated neutral wire for the 120 volt light.
- Low Voltage Lighting as a Safer Lighting Source
The advance in lighting technologies now provide several low voltage alternatives to be considered as a replacement light source.
More about Electrical Wiring Codes
Electrical Code Articles for Home Wiring
Electrical Code Directory covering AFCI circuit, electrical-boxes, electrical-circuit, electrical-code-outlets, electrical GFCI, electrical grounding, electrical project, electrical-services, electrical-underground, electrical-wiring, electrical-wiring-code, lighting-code, and smoke-detectors.
GFCI Outlet Wiring
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electric, NEC 680-20 Pool Light, Pool Equipment and Home Electrical Wiring:|
|« Previous||Next »|
|Light Fixture and Ceiling Fan Switch Wiring||Common Electric Appliance Repair – Espresso Machine|
I am adding a section of the tubing/conduit that the 16/3 water resistant electrical cable is in from sub pool light J-box to pool light and wondering what type of tubing this is. It looks like copper but it is very thick walled. Is this in fact copper and what do I ask for when I go purchase it?
I have been told that I have a porch light too close to my swimming pool. Is it sufficient to put the light on a GFI
The NEC Code 680.22B3 requires that a light fixture is permitted by pools if it is:
(1.) Protected by a GFCI circuit.
(2.) Greater than 5 feet from the edge of the pool.
(3.) Greater than 5 feet high.
Please note all three conditions that must be met.
I am a first-time pool owner and am learning all of the nuances of owning a pool. My pool light recently went out and we had a pool guy come out to replace it. He tried to see if the GFCI needed to be reset but we do not have one. Our house was built in the 60’s and the pool is probably about the same age. He would not replace the light and recommended an electrician. The problem is that we are renting right now. I called the property manager to let him know and he is sending out his handyman to add a GFCI receptacle at the junction box, not an electrician. Will this provide the protection that we need? The light looks like a standard pool light and it is wired into a junction box a few feet from the pool. Then it goes to a breaker box by the pump that is dedicated to the pool equipment (pump and light only). The light has to be turned off/on at the breaker box, as there is no other switch. Thank you for any feedback and I can provide any additional information if needed.
Hi Josh – Great Question!
In a situation like this it would be best to have a licensed electrician install the necessary GFCI protection for the pool light, and at the same time take a look at all of the electrical wiring and devices in the area of the pool, and then make recommendations about anything that is not up to current electrical code standards. Although there are some very good handyman workers that do a variety of fine work, they are not typically not licensed electricians.
I hope this helps,
Anyone can install a GFCI, since in most cases a permit MUST be pulled and the building Inspector will either pass it or fail the job.
Do you have to have a brass or plastic pool light J-box with a #8 in the pool light enclosure if the house is old, or can it go in to a bell box above the water line.
NEC Codes apply regardless of the age of the home or the age of the pool. Proper grounding and GFCI protection is of utmost concern, both for inside the pool, the surrounding area of the pool, and any equipment that is installed in or around the pool location. Light fixture assemblies and cords should be UL Approved for Pool Locations as it applies to the intended installation.
For your application be sure to review all the applicable NEC Codes for your project, with special attention to NEC Article 680.2.