Wiring for GFCI Outlets
How can I wire a GFCI Outlet with no ground wire? Installing a GFCI Receptacle Where a Ground is Not Available.
GFI Outlet Wiring
Electrical Question: How can I wire a GFCI Outlet with no ground wire?
I was trying to change two plugs to GFCI plugs.
- Each is on a different circuit. The first plug is the only one on the circuit.
- There are only 2 wires, no ground. Can I attach these to the GFCI with no ground?
- Will it work properly? The second plug has another plug on the line after it, so 2 wires in and 2 wires out, but again no ground.
- This is in the kitchen of my office building. The city wants these to be both GFCI. Do I need to add a ground?
This electrical wiring question came from: Dan, a Homeowner from Santa Maria, California.
Thanks for your electrical wiring question Dan.
GFI Outlet Wiring Without a Ground Wire
Application: GFCI Wiring.
Skill Level: Beginner to Intermediate – Best performed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the number of outlets that will be replaced.
Precaution: Identify the outlet circuit, turn it OFF and Tag it with a Note before working with the wiring.
Installing a GFCI Receptacle Where a Ground is Not Available
- It is always best to install a ground wire or upgrade the electrical wiring however a GFCI may be installed where there is not a ground wire available as long as it is installed according to code and marked clearly that the receptacle does not have a ground.
- The GFCI receptacle will still provide protection due to the way the circuitry is designed.
More about GFCI Outlet Wiring
For more information about GFCI Wiring
How to Connect GFCI Wiring
- GFCI Wiring
- This list of articles will help you learn about the features and benefits provided by GFI Outlets.
- GFCI Receptacles and how they are wired.
- Electrician Explains Electrical Codes for GFCI and GFI Home Wiring with Photos, Wiring Diagrams and Answers to Your Questions
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring, GFCI and Home Electrical Wiring:|
|« Previous||Next »|
|Why Circuit Breakers Trip Off and What To Do Next||Wiring for a Electric Panel in a Pump House and a Home|