Why Outlets Stop Working
What happened to make my outlets stop working? How to Identify and Repair Outlets, The most common reasons why wall outlets stop working and how they are repaired.
Outlets that Lost Power
Electrical Question: What happened to make my outlets stop working?
The following electrical questions have similar problems where power was lost to outlets. The typical cause for lost power to outlets and and methods of repair are described below.
Why did the outlet stop working?
I usually try to fix stuff before I call a pro, but this electrical outlet has got me stumped.
- Someone plugged a hairdryer and a space heater into a standard duplex bathroom outlet at the same time, and the outlet stopped working.
- The breaker didn’t trip.
- Both the standard outlet and another GFI outlet next to it are not working.
- These broken outlets share a breaker with 3 lights and a vent, which are still functional.
- The bathroom also has a functioning GFI outlet, so we’re making due.
- The broken GFI has 3 sets of wires going to it.
- One wire pair reads 1.2 volts 60 Hz when the breaker is closed, but 2.4 volts 60 Hz when the breaker is open.
- The other GFI wire pairs and the wire pair in the standard outlet have a minimal voltage on them.
- I can’t see much of the wiring, some of it is visible in the attic, but much is concealed in the walls.
Any ideas what happened?
This electrical wiring question came from: Elliot, a Homeowner in Florida.
What could the problem be with out Outlets?
- All outlets in room not working but 1/2 of one, breaker not blown in box.
- My wife turned on lights in morning and turned right back off, left room and returned a few minutes later and turned back on only one lamp was on and it popped and went out.
- Outlets are fixed where top is controlled by wall switch and bottom is hot all the time.
- We have checked all outlets and no wires are loose or look burned. What are your suggestions?
This electrical wiring question came from Wayne in Indiana.
Thanks for your Home Electrical questions Elliot and Wayne.
How to Troubleshoot Outlets that Lost Power
Identify and Repair Outlet Problems
Application: Testing Outlet Circuit Wiring
Skill Level: Intermediate to Advanced – Best Repaired by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools a Voltage Tester or Plug-In Circuit Analyzer.
Estimated Time: Depends on personal level experience, ability to work with tools, the extent of the electrical repairs, the number of outlets that are affected and access to each location.
Precaution: Identify the GFCI outlet circuit, turn it OFF and Tag it with a Note before working with the wiring.
How to Troubleshoot Electric Outlet Problems
The following is a list of problems that may prevent electrical outlets to stop working, and where to locate these potential electrical problems.
- The most common reason why residential home outlets stop working is due to a break down that occurs within the electrical circuit of the outlet.
- Most typically it is found that a wire connection that is made in or onto one of the outlets that is a part of the circuit has deteriorated to the point of burning apart from the connection.
- Some of the connections that are burnt apart were incorrect wiring additions to the existing circuit, or the push-in connections to the back of a receptacle outlet overheat and finally let go.
- Outlet circuits may be affected when high consuming devices are used such as space heaters and vacuum cleaners which demand high amounts of power which is passed through many of the devices between the outlet and the electric panel.
- It may also be discovered that the GFI outlet has been affected and may require replacement.
- In some cases an electrician will discover problems with the outlet circuit in the electrical panel where either the neutral wire or the power wire to the circuit breaker has burnt wire due to a loose or overloaded condition of the circuit.
Repairing Burnt Electrical Wire on an Outlet Circuit
- Before working with electrical wiring for any reason the circuit must be identified, turned off and tagged with a note indicating that work is being performed.
- Burnt electrical wire must be trimmed away so a fresh connection may be made with clean wire.
- If the affected wires become too short then additional wire of the same size and type of insulation may be spliced using UL approved wire connectors.
- If an outlet device or switch was affected and has burnt terminal connections then it should be replaced with a new device with the same electrical specifications.
More about Wiring for Electrical Outlets
- Wiring Electrical Outlet for the Home
- Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Wiring a GFI
Wiring Diagram GFI
- The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
- Electrical Wiring Protection using Circuit Breakers
- A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
- Electrical Wire for the Home
- Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about electrical circuit, Outlets Stopped Working, Troubleshooting and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Circuit for a Tanning Bed||Installing or Upgrading Electrical Wiring|