Why Christmas Lights Make the Outlet Trip Off
Why do my Christmas lights keep tripping the outlet outside of my house? Common Problems that Cause Christmas Lights to Turn Off.
Outdoor Christmas Lights
Electrical Question: Why do my Christmas lights keep tripping the outlet outside of my house?
- I have my Christmas lights plugged into an outlet outside of my house.
- The lights stay on for a few hours and then go out.
- To turn the outlet back on I press the reset button on a GFCI outlet that is in my garage GFCI.
- This makes the outside outlet work again, but then the lights keep keep going out.
This electrical wiring question came from Evelyn, in Land o Lakes, Florida.
Thanks for your electrical wiring question Evelyn.
How to Troubleshoot Outdoor Christmas Light Problems
Common Problems that Cause Christmas Lights to Turn Off
Background: Outdoor outlets are required to have GFCI protection, and as with this question, the outside outlets are protected by a GFCI outlet which is located in the garage. When the GFCI outlet continues to trip off this will indicate that there is a problem that needs to be identified. The following will help you identify the most common problems with outdoor Christmas lights.
- Problem with the Outdoor Receptacle Outlet Cover
- Outdoor outlets must have a cover that is considered weatherproof when a cord is plugged in. This is made possible by installing a bubble type cover that will allow a cord to enter through an opening in the bottom of the cover while the cover is closed and covering the outlet.
- Bubble covers are considered to provide in-use protection for outlets while a cord is plugged in which will prevent moisture from causing the GFCI from tripping off.
- Christmas Light Problems
- Cracked or worn out wiring of the light strand may cause a voltage leakage which can lead to a ground fault.
- Installing Christmas lights using bare metal staples or nails can damage the wiring. Consider using insulated fasteners to secure the lights in place.
- Make sure the Christmas light strands are rated for outdoor use.
- Moisture from Ice, Snow, and Rain
- Christmas lights that are installed on the home are best located under the eves or areas where the roof overhangs to provide protection from weather elements.
- If the GFCI outlet trips off after the lights have been on for a while, this may indicated that the heat of the lights is causing snow or ice to melt and create moisture which can cause the GFCI to trip off.
Additional resources about GFCI Outlets and Christmas Lights
- GFCI Code Requirements
- This article explains the basics of the electrical code requirements for GFI Protection as part of the home electrical wiring system.
More about GFCI Code Requirements
- GFCI Circuits and Outlets
- This article about GFCI outlets for home electrical use will provide a more in depth understanding about gfi protection and provides wiring examples.
More about GFCI Circuits and Outlets
- Hanging Christmas Lights
- Dave gives some tips about how to install Christmas lights and holiday decorations.
More about Hanging Christmas Lights
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|« Wiring for an Electric Range Circuit||Can a 125Amp Circuit Breaker be used for 250Amps? »|