Why an Outlet Circuit Turns On and Off
Why does an outlet cut out and then it comes back on? How to Repair Outlet Circuit Problems, Common Receptacle Outlet Problems and How to Fix Them.
Electrical Outlet Circuit Problem
Electrical Question: Why does an outlet cut out and then it comes back on?
I have this outlet that has a Yamaha or Bose home theater receiver that when I raise the volume below -30 dB, the power in the outlet blows the circuit. The receiver is 400 watts.
- I switch them from time to time, but they are never plugged in at the same time.
- The Bose will cut the outlet at about the same volume.
- The outlet will cut but then about 30 seconds later, it comes back on, the circuit never trips, even after I check.
- I do have a dehumidifier on the same line, and I think that it blew the circuit and permanently damaged the line.
- The dehumidifier has tripped the circuit but the problem was gone after I turned the dehumidifier off.
- The outlet persists to cut out with the dehumidifier unplugged.
This electrical troubleshooting repair question came from: Andrew, a Homeowner from Long Island, NY.
Thanks for your electrical troubleshooting question Andrew.
How to Repair Outlet Circuit Problems
Application: Troubleshooting an Outlet Circuit.
Skill Level: Advanced – Best performed by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester or Volt Ohm Meter.
Estimated Time: Depends on the type and age of the electrical wiring and the access to the circuits and wiring to be evaluated.
Precaution: This is a project that should be performed by a Licensed Electrical Contractor and typically requires specific tests of the electrical circuits.
Notice: Repairs to Home Electrical Wiring should be done according to local and national electrical codes and installing new or replacement electrical parts or equipment may require a permit and inspections.
Common Receptacle Outlet Problems and How to Fix Them
- Inspecting Outlets
This circuit should be turned off and then all of the outlets on this circuit would need to be removed so that the electrical wiring can be inspected which will no doubt revel a loose or deteriorated connection or a bad splice.
- Heavily Used Outlets
Special attention should be given to the outlet where the dehumidifier is plugged into and the outlet in the surrounding areas.
- Quick Connect Outlet Problem
If the outlets have quick connect wiring where the wires are pushed into the back of the outlets then there may be a connection that has deteriorated.
- Replacing and Repairing Burnt Wiring
If this is the case then the outlet will need to be replaced and the wiring repaired as needed.
- Connecting to Screw Terminals
The quick connect feature should not be used where high watt devices are used such as space heaters and dehumidifiers.
- Pig Tailed Wire Splices
Instead the individual wires should be pig-tailed or spliced so that the circuit does not floe thorough the outlets.
More about Wiring Outlet Circuits and Repairs
Wiring Electrical Outlet for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
For more information about Outlet Wiring
Troubleshooting and Repairing Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repair, Electrical Troubleshooting, Outlets, Troubleshooting and Home Electrical Wiring:|
|« Previous||Next »|
|Installing Dimmers for 3 Way and 4 Way Switches||Wiring for an Electric Range Circuit|