Why a Neutral Electrical Circuit Wire May Be Hot
What could be causing the copper ground and neutral wire be hot? Power went out in bathroom and I checked the circuit breaker, and the GFCI and it seems fine.
Causes of Neutral Wires to Have 120 Volt Readings
Question:What could be causing the copper ground and neutral wire be hot?
Power went out in bathroom and I checked the circuit breaker, and the GFCI and it seems fine. When I investigated power and wiring in light switches and outlets, I found the ground (copper wire) and the neutral (white) has 120v. Everything I have checked seems ok, even making sure the ground into the house looks good. What could be causing the copper ground and neutral wire be hot? Is there anything I need to check?
This electrical question came from: Daniel, a Handyman from Mount Vernon, Washington.
See more about Home Wiring for Washington
Thanks for your electrical question Daniel.
Understanding the Neutral Electrical Wire
Daniel, depending on the circuit wiring and the circuit components, it is common to get a 120 volt reading on a neutral wire that is tested to ground. Such is the case with a lighting circuit where there are fixtures with standard incandescent light bulbs. A 120 volt reading will be noticed if voltage tester leads are placed between either two hot wires or two neutral wire when the circuit is on and under load. (It is not recommended that this procedure is performed unless you understand what you are doing, because getting in the middle of any live circuit can cause an electrical shock which could be fatal.) Readings of 120 volts on a neutral may also be due to one leg of the electrical service or a circuit that has been lost, therefore a voltage feedback is occurring through other devices with the electrical circuit. When such conditions have been detected, it is best to contact a qualified electrical contractor who will identify the problem and then perform the necessary repairs.
More about Electrical Wiring
electrical outlet wiring
Wiring Electrical Outlet for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
How to Install Bathroom Electrical Wiring
Bathroom Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Bathroom Electrical Wiring with Code Requirements for most new or remodel projects.
For more information about Troubleshooting
Troubleshooting Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Understanding Cable Size for Home Wiring||Allowed Conduit Type for a Home Electrical Panel »|