Sub Panel Grounding and Neutrals
Understanding Grounding for Sub Panels: When you add a second electrical panel with separate neutral and common bars, do you ground the common to the box along with a ground rod connection?
Understanding Grounding for Sub Panels
[ad#block] Question: When you add a second electrical panel with separate neutral and common bars, do you ground the common to the box along with a ground rod connection?
This electrical question came from: John, a Homeowner from Manitowoc, WI.
See more about Home Wiring for Wisconsin
Additional Comments: I have recently retired due to a disability. I just love this site thank you so much.
Thanks for your electrical question John, I hope your doing well, and Thanks for the nice complement.
This article refers to sub panels that are located in an attached building, or the same building structure. For information about a sub panel located in a detached or remote building please see the following article which discusses the topic of grounding for a Detached Building in detail: Installing a Sub Panel for a Detached Building
Grounding for a Sub Panel Located in the Same Building
- A second panel or sub panel should have the neutral and ground terminals or bars isolated from each other, this is why the main circuit feed to the sub panel must have 4 wires, with a dedicated insulated wire for the neutral and a separate wire for the ground.
- All the ground wires bond back at the main panel together with the neutrals.
- The sub panel neutral bar or terminal should not be bonded to the enclosure or the ground of the sub panel. The sub panel ground should not have a ground rod tied to it.
- The bonding for the main ground sources such as a ground rod is made at the main panel where all the grounds are bonded together as well.
The Following links will assist you with Grounding for Sub Panels
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Grounding Methods and Requirements
Listing of electrical codes for grounding with examples of electrical grounding codes for home electrical wiring.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Grounding and Home Electrical Wiring:|
|« Previous||Next »|
|The Key to 4 Way Switch Wiring||Why Lights Flicker and Then Go Off|
Please explain how 2 ground wires came in to being.
How do you ground something TWICE? It’s either grounded or it’s not.
In a home electrical system there is typically a main ground source, which is located at the main panel. The main panel is where all grounding methods are bonded together. This article about sub panels refers to the separation of the ground and the neutral which is required by the NEC electrical code.
Thanks for your question about electrical grounding,