My circuits do not work right, is my electrical fuse box safe?
How to Solve Old Electrical Fuse Box Problems: How Unbalanced Circuits may cause one of the cartridge fuses to blow which will affect half of the 120 volt screw infuse circuits.
Upgrading an Old Electrical Fuse Box
Electrical Question: I recently moved into a house that has a fuse box and is running window air conditioning units.
- The first day in the house everything worked fine, the second day the window unit in the front room went out.
- When it stopped working I lost power to my porch light, entry light, washer and dryer, range, dishwasher, and kitchen lights.
- When I plug the new window a/c unit into the same outlet it will run for a few seconds and then turn off.
- The second before it turns off the lights in the kitchen flash. This does not blow the fuses (for the AC outlet which is wired into a circuit with two fuses) and I am able to turn the a/c unit back on and the same thing happens.
- We have cleaned up the grounds in the fuse box (yes fuse not breaker) thinking that maybe the a/c was creating a ground that the appliances weren’t getting. We made sure the range had solid connection to both ground and power, the range is a 220 volt with a fuse slot of its own, the same as the washer and dryer.
- I am at a loss as to why it is happening, since all the things that are off, are all on different circuits.
Hopefully this is enough information to get some ideas.
Thank you for your time.
Additional Comments: Great resource for people to get opinions before forking out lots of money on problems!
Background: Eric, a Handyman from Topeka KS.
Thanks for your electrical wiring question Eric.
Old Electric Fuse Boxes and Circuit Problems
How Unbalanced Circuits Can Cause a Fuse to Blow or Circuit Breaker to Trip
- Electric Fuse Boxes
- Some fuse boxes have two sets of cartridge fuses where one supplies 60 amps 240 volts to the kitchen range while the other supplies power for the screw in type fuse protected 120 volt circuits.
- Unbalanced loads may cause one of the cartridge fuses to blow which will affect half of the 120 volt screw infuse circuits.
- Electrical Safety Inspection and Evaluation
- My first thought about you have described is that there is a problem at the main electrical fuse box.
- I would have the main fuse box inspected for loose or deteriorating connections.
- Electrical Service Upgrade
- My recommendation is to upgrade the electrical service to a new circuit breaker panel as soon as possible.
- A safety inspection of the home electrical wiring system and the main ground would be a very good idea and should include checking for the presence of smoke detectors and GFCI protection in the required areas.
More about Home Electrical Wiring
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Wire Connections for a 3-Wire Range Cord with Video||How To Ground a Television or Communications Antenna|