Minimum Height for Electric Service Meter
What is the minimum height for mounting an electric service? Mounting the Electric Service Meter.
Electric Service Meter
Electrical Question: What is the minimum height for mounting an electric service?
- Is there a minimum height for mounting of service meter on side of house.
- New underground service and the new service/meter is 43″ to top of can.
- My understanding is all panels should be mounted 60″-72″ above finished grade.
This electrical wiring question came from Anthony, in White Pine, Tennessee.
Thanks for your electrical wiring question Anthony.
Installing an Electric Service
Application: Installing an Electric Service.
Skill Level: Advanced – Best installed by a Licensed Electrical Contractor or a Certified Master Electrician.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for the specific method of electrical service installation.
Estimated Time: Depends on the type of panel, the location, and available access to the project area.
Precaution: This is an extensive project. Working in an electric panel has possible arc flash hazards and should be performed by a Licensed Electrical Contractor.
Notice: Installing an Electrical Service Panel should be done according to local and national electrical codes with a permit and be inspected.
Mounting the Electric Service Meter
- The Minimum Height for an Electric Service Meter is actually specified by the local electric utility provider or the power company.
- The NEC National Electrical Code does not specify a minimum height for a service meter, however the typical minimum height for mounting a service meter on side of a house is 5 to 6 feet above the finished grade or level ground.
More about Electrical Services
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electric Meter, Electrical Code NEC, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Installing a Workshop Panel for a Welder||Ceiling Fan Rotation for Energy Savings|