How to Use Switched Outlet Wiring for a New Ceiling Fan
This can be done but the wiring configuration must be identified and verified. Be aware that there may be more than one…
Electrical Question from Jim about Light Switch Wiring
Received from Jim a Homeowner in Mentor. Ohio
Question: I’m installing a ceiling fan. The switch in the bedroom controls an outlet. I want to wire the fan so it is controlled by the switch. I also want the outlet to be constant hot but not controlled by the switch.
Thanks for your electrical question.
This can be done but the wiring configuration must be identified and verified. Be aware that there may be more than one switched outlet in the room that will be affected.
Basically this is a process ofÂ changing the wiring configuration at the outlet that is controlled by the switch. The wire returning from the switch will need to become a neutral wire and the power wire will need to take its place on the outlet to make that portion of the outlet is powered all the time. This will provide both power and neutral at the switch box which is required for the ceiling fan. A new cable will need to be installed from the wall switch up to the ceiling fan location. This wire can be a 3-wire type cable that could provide separate switching for the fan and the light. A double switch may be purchased which will install in the same size box and provide variable speed control for the fan and a dimmer control for the light.
An approved Ceiling Fan box must be installed and well supported.
Additional wiring must match the existing wire gauge and type.
Follow this link for complete details and Wiring Diagrams for Installing Ceiling Fans
The Following links will assist you with your electrical question:
For more information about Light Switch Wiring
Light Switch Wiring
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Ceiling Fans, Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Lights Dim Out Very Often – Help!||What is the Rated Ampacity of Copper AWG 4-3 Romex?|