How to Splice Direct Buried Electric Cables
Is there a way to cover spliced wires and lugs to prevent damage? Repairing Direct Burial Electrical Cables.
Splicing Buried Electrical Cables
Electrical Question: Is there a way to cover spliced wires and lugs to prevent damage?
- I am working with a electrical service panel that feeds another service panel.
- I have a 200 Amp panel with a 100 Amp breaker which has three #2 gauge wires running to a secondary electric service box.
- The problem is that the #2 wires are direct buried cables.
- When uncovering them next to the house I found that all three cables have been spliced in the same location.
- My question is how can this be made safe? Is there some way to cover the bare spliced wires and lugs to prevent any kind of short since they are all three buried close to each other?
This home electrical repairs question came from: Ray, from Milton, Florida.
See more about Home Wiring for Florida
Thanks for your Electrical Repair question Ray.
Splice Direct Buried Electric Cables
Application: Splicing Underground or Direct Buried Electrical Cables.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester Ground or Trenching Hand Tools.
Estimated Time: Depends on the personal level experience and ability to work with tools, condition of the soil or environment for access to the cable or electrical wiring.
Precaution: Identify the affected power source, turn it OFF and then Tag it with a Note before performing any wire splicing or cable repairs.
Special Materials: Depending on the final enclosure to protect the splices, Moisture proof or Water Resistant Materials including Properly sized wire connectors, anti-corrosion ointment, electrical tape, shrink tubing or other materials to perform an approved splice method.
Protection for Buried Electrical Cable Splices
- The direct burial splices must be made properly using a corrosion inhibitor and then well insulated.
- The splices should be accessible as well which could be accomplished by installing a concrete box, such as a Christy Box with a concrete lid or a traffic rated lid if this is in a traffic area.
- The concrete box may be placed over the splices after the splices have been made.
- The buried cables should be checked to see if they are properly rated for Direct Burial and the cables should be buried a minimum of 24 inches deep.
- Open splices such as this should be repaired right away to eliminate a potential shock hazard!
- The circuit should be turned OFF until the condition has been resolved.
More about Repairing Direct Burial Electrical Cables
The Scotch Cast repair kit provides maximum protection for the electrical wiring repairs and moisture proofing for direct burial electrical cable. This kit is available in a wide variety of sizes for several applications. The 3M Scotch Cast Kit is available in a wide variety of sizes.
Testers to Help Solve Electrical Problems
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|« How to Install Electrical Wiring for a Bathroom Remodel Project||Rewiring for Bedroom and Living Outlet Circuits »|