How to Repair a GFI Outlet Circuit
How can I fix a problem with my GFCI circuit? How to Troubleshoot and Repair GFI Outlet Circuit Wiring.
Steps for Testing a GFCI Outlet Circuit
Electrical Question #1: How can I fix a problem with my GFCI circuit?
I have a problem with the GFCI circuits in my home.
- The end of the GFCI line is in the garage and before that the bathroom which joins the garage. I cannot get power to either.
- The line coming out of my panel leads to a GFCI outlet, about one foot away.
- There’s power coming out of the “load” line.
- Here’s the problem, sometimes I do get power to both outlets in the bath and garage, then, when I plug in a device (lead light) in the garage the light goes on initially then dims and goes out. Then I got no power to the bath or the garage.
- Power is still on coming out of the GFCI outlet next to the panel box.
- Fearing there might be a wiring problem, maybe to a switch, I’ve turned all switches in the house on and that doesn’t connect.
Thank you for your advice.
This electrical wiring question came from: Jerry, in NY, New York.
Electrical Question #2:
- I have a GFCI outlet that stopped working from outside. There is another non GFCI outlet also outside that is now working and had not before the GFCI tripped. I checked the main breaker box and no breakers are tripped and the GFCI outlet cannot be reset.
This electrical wiring question came from Ray in Sulphur, Louisiana
Electrical Question #3:
- I am replacing an outlet. The wires were not marked. I checked them with voltage indicator and marked the set with power. I then followed instructions on installation. When everything was in place, flip breaker and no power. I pulled it apart and no I have no power to either line. Any suggestions?
This electrical wiring question came from Rick, a Homeowner in Eagan, Minnesota.
Thank you for your electrical wiring questions.
Troubleshoot and Repair GFCI Outlet Circuit Wiring
- Skill Level: Intermediate to Advanced, best performed by a licensed residential electrician.
- Tools Required: Basic Electricians Pouch Hand Tools a Voltage Tester or Plug-In Circuit Analyzer.
- Estimated Time: Depends on personal level experience, ability to work with tools, the extent of the electrical repairs, the number of outlets that are affected and access to each location.
- Precaution: Identify the GFCI outlet circuit, turn it OFF and Tag it with a Note before working with the wiring.
How to Test a GFI Circuit
When the GFI circuit seems to be partially working or not working at all here are some things to double check to get the GFCI working again.
- Check for Loose Wires
Make sure there are no loose wires within the circuit, especially the white neutral wire.
- Incoming Power Source: The LINE
Make sure the incoming power source to the GFCI outlet are attached to the LINE side as indicated on the back of the receptacle.
- Outgoing Power Source: The Load
Make sure the outgoing circuit wiring is connected to the LOAD side of the GFCI Outlet.
- LINE and LOAD Wiring
Both the black and white wires must be connected separately into the appropriate terminals of the LINE and the LOAD side of the GFCI Outlet or GFI Receptacle.
- A Bad GFI
If the wiring connections are correct and the circuit voltage is normal then the GFCI outlet may be faulty and should be replaced.
- Checking the Circuit Polarity
The integrity of the GFI circuit wiring may be tested for voltage by temporarily removing the GFCI outlet and splicing the wires through and then testing the voltage and polarity at each receptacle outlet of the same circuit. If the voltage readings and polarity test is normal then the GFCI is faulty or the connections to the GFCI were incorrect.
- Plug-In Circuit Analyzer
A plug in circuit analyzer will be helpful to determine the correct wiring of the circuit and help detect circuit faults.
Important Note about Ground Fault Circuit Interruption:
Both GFI and GFCI are basically the same and both provide protection against ground faults by interrupting the electrical circuit by sensing voltage that passes to a ground source.
More about Wiring a GFCI
- How to Wire GFCI Outlets
GFCI and GFI Wiring Diagrams
- The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
- Electrical Outlet Wiring
Wiring Electrical Outlets for the Home
- Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
- Basic House Wiring Circuits
House Wiring Circuits and Circuit Breakers
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
- Using Testers to Identify the Cause of why Electrical Power has been Lost
Testers Help Determine Conditions that Lead to Electrical Power Loss
- Troubleshooting to Find Out Why Your Home Lost Power
How to Identify Lost Power
- Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Types of Electrical Testers
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repair and Home Electrical Wiring:|
|« Previous||Next »|
|How to Avoid Damaging Electrical Cables Inside Walls||Why Is My Bathroom Light Fixture Not Working?|