How To Fix Light Switch Wiring
Is your light switch not working? Here is the testing method for checking light switches and wiring….
Testing Method for Fixing Light Switch Wiring
Electrical Repairs Question
Hi I am working on my brothers house to try and help him with his electrical. It is all Romex, the house was built in the 198o’s etc. The problem is when you push the light switch to on in the bedroom the light switch buzzes and immediately trips the breaker. If I reset the breaker all other lights and receptacles work on this circuit as long as the switch to the bedroom lamp is not turned on. I removed the light and fan in the bedroom and pulled the switch from the wall and checked the wiring to both. I then disconnected the light completely and moved the wires far apart and capped them. I pulled the switch out from the plastic new work box and moved all of the wires away from each other. Hit the switch again and it tripped the breaker. This is where I am unsure. Does this mean the short is in the wire from the light switch to the fixture? It appears it is wired straight from the switch into the attic to the fixture. Could any other component in the circuit effect this? If not should I replace the 14/2 from the fixture to the switch?
Thanks for your time. I appreciate it.
This electrical question came from: Greg, a Handyman from Hixson, Tennessee.
See more about Home Wiring for Tennessee
Additional Comments: Very nice website. I read through the trouble shooting and enjoyed it.
Thanks for your Electrical Repairs Question Greg.
Testing a Light Switch and Wiring
Greg, there may be a few possibilities that are causing the problem, all of which can be identified using an ohm meter.
- Basically what you need to do is identify each wire set and verify the connections to make sure they are correct.
- If there are two wires from 2-wire cable that are attached to the switch and if these two wires are not connected correctly back at the fixture box then you may be switching a hot and a neutral together and blowing the circuit.
- The other possibility is that a nail has been driven into and across a cable which could be creating a short between a switched leg and the ground wire. Using an ohm meter to check the cable between the switch and the fixture box will reveal exactly what is happening.
- These test should be done with the circuit turned off. This test with the ohm meter is basically a continuity test to verify the cable and see if there is a short between any of the wires, The test should be done with the wires removed from the switch and the light fixture and the wires apart from each other testing wire to wire to see if there is a short.
- If that test proves OK then the test of placing a wire connector with both insulated wires together to see if you have continuity through the two.
- Your basically creating a loop and making sure you have continuity which will verify this.
- Once these tests are made you will no doubt understand more about the circuit wiring and if there is in fact a problem with the wiring which may require you to replace the cable if it is damaged.
The Following will assist you with your Electrical Repairs
Using electrical testers
Electrical Safety and Voltage Testers
When working on home electrical wiring, quality voltage testers can play an important part in electrical safety. Electrical testers enable you to identify electrical circuits and help prevent the possibility of accidental electrical shock.
You identified your project to be about Troubleshooting, so you might find this information useful:
Troubleshooting Electrical Wiring
Licensed Electrician Reveals the Secrets of Successful Electrical Troubleshooting Methods used to solve the majority of the home electrical problems and wiring failures encountered.
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Electrical Wiring Protection using Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Light Switch Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Why Wall Sockets and Outlets Stop Working||Federal Pacific Circuit Breaker Alternate|