How to Activate a Garage Light from the Garage Door Opener
Here is a easy solution to activate a separate garage light that would be triggered by the garage door opener using a socket adapter that can be connected to any light fixture and operated by your garage door opener.
Garage Light Activated by the Automatic Door Opener
Electrical Question: Is there an RF switch system I can use to turn on a light near my garage door lift motor and light?
The light would be nearby & plugged into an unswitched wall outlet.
The garage door opener light is too dim, so I want to trigger a brighter light.
I would envision the fr switch to be triggered by the opener light circuit that comes on when the door is opened or closed & shut off when the opener light shuts off automatically after a minute or so.
This electrical wiring question came from: John, a Homeowner from Bellevue, Washington
See more about Home Wiring for Washington
Thanks for your electrical wiring question John
Garage Light Activated by the Automatic Door Opener
Intermediate to Advanced
Basic electrician’s pouch, for finish wiring
Here is a easy solution to activate a separate garage light that would be triggered by the garage door opener
- Screw in A-base light bulb socket adapter with 2-wire leads.
- Junction box enclosure and cover, 6 x 6 x 4 inches.
- Insulated cords connectors.
- 14-3 SO or SJ cord.
- 120 volt SPST Relay, 15 amp contacts, 60 watt or less coil.
- Relay base for above relay.
- A power cord, 120 volt, 15 amp rated, 4 to 6 feet long, same as used for dishwashers and disposals.
- The additional light fixture you have in mind, my choice would be a surface mounted 4 foot, 2-tube fluorescent shop light style.
- Identify and disconnect the power to the garage door opener circuit.
- Remove the door opener light bulb.
- Insert the a-base light bulb adapter.
- Mount the junction box near the garage door opener making sure that is will not be affected by the door opener or the travel of the garage door system or moving parts.
- The lead wires from the A-base socket adapter would be routed to the junction box and should be protected between the door opener and the junction box using flexible PVC conduit and connector hardware, as per the installation.
- Mount the new fluorescent light fixture close to the junction box using wood screws to ceiling joists of use toggle bolts.
- The plug on cord of the shop light would be removed and the cord inserted into the junction box using an insulated cord connector.
- The pigtail cord would be installed into the junction box using using an insulated cord connector.
- All the ground wires must be connected together and bonded to the junction box enclosure.
- Mount the relay base into the center area of the junction box.
- Connect the power leads from the A-base socket adapter to the relay coil terminals on the relay base.
- The neutral wires of the power cord and the light fixture cord are connected together.
- The remaining wire of the power cord connects to the terminal on the relay base of the “COMMON” of the SPST Contacts.
- The remaining wire of the light fixture cord connects to the “NO” (Normally Open) of the SPST Contacts.
WRAPPING IT UP
- Plug the relay into the relay base.
- Place the cover onto the junction box.
- The Pigtail will plug into the same power source as the garage door opener, typically a ceiling mounted duplex receptacle.
- The new light fixture will now be operated by the garage door opener.
Altering the garage door opener and the cord of the light fixture may void their warranties.
Understanding Electrical Relays
The use of relays that are sometimes needed to control special device loads such as Air Conditioners and other high demand equipment from starting at the same time.
Wiring Electrical Outlets for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Garage Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Garage Electrical Wiring with Code Requirements for most new or remodel projects.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Fluorescent Lighting Problems and How To Fix Them||Installing A Fireplace Electrical Outlet|