Fix Three-Way Light Switch Wiring
My Three Way Switches are not working right, How should the Wiring Connections be made? How to Connect Wires for 3-Way Light Switches.
3-Way Light Switch Wiring Correction
[ad#block]Electrical Question: My Three Way Switches are not working right, How should the Wiring Connections be made?
Two switches control the same light fixture. One is a triplex switch, outside the bathroom. The other is a single switch, inside the bathroom.
- Do you think the wiring is wrong, or do I need to buy a new switch? How would it be fixed, if it is wrong?
- When Triplex is in the OFF position, The single switch does not operate.
- When Triplex is in ON position, The single switch operates normally.
- When Single switch is in ON position, The triplex does not operate.
- When Single switch is in OFF position, The triplex operates normally.
Background: Stephen, a Homeowner from Toronto, Ontario, Canada
Thanks for your electrical wiring question Stephen.
How to Connect Wires for 3-Way Light Switches
Yes Stephen, the wiring for this three way switch is definitely wrong.
- Both of the switches should be 3-way switches with the appropriate wiring installed between them, such as a 3-wire cable.
- The power source and the switch leg to the light fixture need to be identified for the exact wiring method.
- See the 3-way switch diagrams by using the links below.
- By the way, your definition of Triplex is the same as a 3-way switch.
The Following will assist you with your 3-Way Light Switch Wiring
How to Wire 3-way Switches
Easy to Understand 3 Way Switch Diagrams
3 Way Switch Diagrams Fully Explained. Detailed Electrical Wiring Diagrams and Pictures assist your Home Electrical Projects.
This link is helpful as a Homeowner
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 3-Way Switch, Wiring Diagrams and Home Electrical Wiring:|
|« Previous||Next »|
|Why A Bathroom Light Fixture May Make Noise||Motor Home Circuit Electrical Troubleshooting|