Essential Electrical Grounding for Pools, Spas and Hot Tubs
What is the right way to Ground Pools, Spas and Hot Tubs? I am installing a packaged above-ground spa. I have a 50amp breaker in my panel feeding a GFI disconnect panel near the spa.
Electrical Grounding for Pools, Spas and Hot Tubs
Question:What is the right way to Ground Pools, Spas and Hot Tubs?
I am installing a packaged above-ground spa. I have a 50amp breaker in my panel feeding a GFI disconnect panel near the spa. All 4 wires from the main panel to the disconnect panel are #6 copper stranded. I had an electrician install the disconnect panel and leave a length (about 16′) of flexible conduit and wires to the spa equipment. I will make the final connection of the 4 wires inside the spa equipment. The manual for the spa specifies #6 copper for common and the two hot wires. They also specify #8 for the ground. My electrician, for some reason, used #10 copper for the ground wire from the disconnect to the spa equipment (about 16′). He says it’s not a problem even though the installation instructions say to use #8. Is he right? Will it be safe to use #10?
This question is from Neil, a Homeowner from Simi Valley, California.
Thanks for your electrical question Neil.
How to Provide Electrical Grounding for Pools, Spas and Hot Tubs
No – this is not safe. A #8 copper ground wire must be installed in place of the #10 ground wire. Furthermore, I would require the electrician to make this correction at his expense siting the specified requirements clearly stated at the spa and due to the fact that the #10 ground wire that was installed is a violation of the NEC requirements for this circuit. The inspection of this project should have caught this, and if you did not do this with a permit then you just placed yourself in a vulnerable position in more ways than one, especially when it comes to spa and pool equipment where essential ground fault devices are required to be installed correctly and according to NEC code for your safety and protection.
I have provided the following links that lead to fully detailed information on this website that will assist you with your electrical question:
More about Electrical Grounding for Pools, Spas and Hot Tubs
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|« Wiring a Ceiling Fan In An Older Home||Troubleshooting Electrical Outlet Problems »|