» Residential Electrical Wiring: Guide to Home Wiring
» Need Electrical Help? Get a Quick Reply! Ask the Electrician
Wiring a Motion Light and Security Camera
By Dave Rongey
How to Wire a Motion Light with a Security Camera
Wire a Motion Light with a Security Camera.
I have two exterior lights wired to one switch inside the house. How can I make one of the light boxes energized all of the time?
I want to wire a Motion detector with a security camera into the box. If the power gets interrupted the camera reset button has to be pressed. I have installed ceiling fans. and lights before. Please Help!
Thanks James O.
Hi James - Great Question.
Here are the options to control one of two fixtures wired to the same switch:
Testing and Investigating - Voltage Tester is needed - The switch box in the house would need to be opened and tested to see if the power originates in the switch box where there is a hot and a neutral OR is there a pair of wires coming into the switch box where the White and Black wires are attached directly to the switch. If the later is true then the power originates at one of the fixture boxes, most likely the closest fixture to the house switch box location.
After identifying the fixture box where the power originates AND if this is the location where the motion/camera is to be located AND if the second fixture is wired through this fixture box THEN you isolate this fixture from the switch leg, wire the switch leg through to the second light fixture and then attach your motion/camera to the originating Hot and Neutral in this fixture box being careful to leave the switch leg wiring in place to maintain the home switch control for the second fixture.
Some Cost Involved, But a Quick Solution:
Purchase an X-10 Control Module and Switch. These devices are fully addressable and work very well together. The wall switch could be a WS467 Wall Switch Module and the light fixture to be controlled apart from the motion/camera could be an Inductive In Line Module - XPFM. This In Line Module is NOT the Plug-In type, it is the type with the wiring to be connected to your light fixture. Using these X-10 Devices would require the original switch to be removed, joining the original wiring which attached to the switch thereby making both fixtures hot all the time
The WS467 Switch will need to be connected to a Hot and a Neutral wire at the switch box. Then installing the XPFM Module inside the fixture box of the fixture to be controlled.
The WS467 Switch and the XPFM Module will need to be addressed identically. Once these devices are installed and addressed the WS467 Switch will operate the outside light fixture and the motion/camera location will remain hot all the time.
The X10 Devices really do a great job. I use them to control the lighting in our home and while we are away a stand-alone controller automatically controls all the lighting giving the appearance that the home is occupied.
There are a lot of great applications X10 can be used for, your situation is one example. You may also want to look into the camera options which give remote control capability as well.
In the location of the proposed motion detect/security camera - Is there a outlet on the wall directly below this outside light? If there is you could extend the outlet wiring up to the location of the outside fixture box and cap off the original fixture wiring thereby isolating these two power sources from each other. This solution is basically a process of locating a circuit in the general location and extending it to the outside fixture box.
More Difficult: If the power originates at the house switch box location the tedious process of installing an additional wire from this switch box out to the fixture box location for the motion/camera. Depending on the layout of the home, attic access etc this would be the last choice.
This should help you get your motion detector light and camera device working and maintain switched control of the outside light fixture.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.