Electrical Code and Buried UF Cable
Does the electrical code allow you to run UF cable in concrete? Installing Buried Electrical Cable, The Minimum Covering Requirements for UF Cable.
Electrical Code for UF Cable
[ad#block]Electrical Question: Does the electrical code allow you to run UF cable inside concrete?
This electrical question came from: Joseph, a Homeowner from Montague, New Jersey.
Thanks for your electrical question Joseph.
Installing Buried UF Electrical Cable
Underground Feeder, UF cable, cannot be run inside concrete.
The Minimum Covering Requirements for UF Cable
- General installation – bury UF cable 24 inches deep.
- 2 Inches of Concrete Covering when UF cable is buried 18 Inches Deep.
- 4 Inch Slab, No Vehicles – 18 Inch Depth.
- Under a Street – 24 Inch Depth.
- Under a Driveway – 18 Inch Depth.
More about Electrical Codes and Electrical Wire Types
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Electrical Code Articles for Home Wiring
Electrical Code Directory covering underground electrical wiring.
The following may also be helpful for you:
Learn more about Home Electrical Wiring
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Code NEC and Home Electrical Wiring:|
|« Previous||Next »|
|Kitchen Countertop Receptacles NEC 210-52||How I Repair a Bathroom Light Fixture that Shorted Out|