Electric Clothes Dryer Double Pole Circuit
Which circuit breaker should be installed for an electric clothes dryer? How an Electrical Circuit is Wired for an Electric Clothes Dryer.
Electric Clothes Dryer
Electrical Question: Which circuit breaker should be installed for an electric clothes dryer?
- I bought a new electric clothes dryer. Everyone says I must have a 30 amp circuit breaker.
- My old dryer has been running on a 20 amp double pole circuit breaker with 10 gauge wire.
- Do I need to replace the breaker with a 30 amp?
- And why the heck did the old dryer run all these years on the 20 amp double pole circuit breaker!
This electrical question came from: Charlotte, a Homeowner in New Jersey.
Thanks for your electrical question Charlotte.
Electric Clothes Dryer Circuit Breaker
Circuit Requirement for an Electric Clothes Dryer
Electric Dryer 30 Amp Circuit and Breaker
- Charlotte, yes – the dryer does require a 30 amp 240 volt circuit.
- If the existing circuit wiring is #10 copper and the cable type is approved for 30 amps then a double pole 30 amp circuit breaker can be installed.
- Why the old dryer ran just fine all those years on 20 amps may be due to the size of the old dryer or a few other factors.
- You may also see if the new dryer installation manual requires a 4-wire circuit instead of the older 3-wire circuit.
More about Wiring a Dryer
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
3-Wire and 4-Wire Configurations for Clothes Dryers
See an electric dryer installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric dryer, or a 3-wire or 4-wire outlet. Lets look a how the electric dryer is wired and what to do if your cord does not match the plug.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 240 Volt Dryer Circuit and Home Electrical Wiring:|
|« Previous||Next »|
|Electrical Wiring for Machinery From Another Country||Is Modifying a Light Fixture Safe?|