Don’t Call an Electrician Until You Try This
How to Reset the Power to a Circuit: I have an electrical problem where the power in a room went off. I replaced the circuit breaker but the problem still exist.
Power Went Off to a Room
[ad#block]Electrical Question: I have an electrical problem where the power in a room went off. I replaced the circuit breaker but the problem still exist.
Last night I was going to watch TV in the bedroom. When I turned on the remote for the TV the power in the room went off. I went to the basement to check the circuit breaker. When I went back upstairs the power still did not turn on. The breaker also was for the bathroom, and the lights going to the basement and the basement. I did go to the electrical store and bought a new breaker and replaced the old one but the problem still exist.
Do you have a solution?
This electrical question came from: Colleen, from Guilford, Connecticut.
Thanks for your electrical question Colleen.
How to Reset the Power to a Tripped GFCI Circuit
Application: Troubleshooting – Testing Electrical Circuit Wiring.
Skill Level: Intermediate to Advanced.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester or Continuity Tester.
Estimated Time: Depends on experience and level of problem solving skills.
Precaution: Testing live wires is dangerous and should be done by an experienced individual only. Testing using a continuity tester should only be made after the circuit has been identified and turned OFF and Tagged.
Resetting a Tripped GFCI Outlet
- From what has been described the solution may be as simple as pushing one reset button.
- The button I am referring to is the RESET button on the bathroom GFCI Outlet.
- NOTE: The Red Button in the picture above is the reset button. The reset button may not be red on some GFCI outlets, however they will be labeled as a Reset button.
- In some cases the GFI Outlet may be in another location, but nine times out of ten the cause of the power being lost as described here is due to a tripped GFCI.
- IMPORTANT: There may be something that is plugged into the circuit which is causing the GFCI to trip off.
- EXAMPLE: To identify a device with a problem, disconnect or unplug specific devices until the GFCI stops tripping.
More about Electrical Problems and Troubleshooting
- Using Testers to Identify Electrical Problems
Testers to Help Solve Electrical Problems
- Troubleshooting Electrical Wiring
- Bathroom Electrical Wiring
Bathroom Electrical Wiring
- Fully Explained Photos and Wiring Diagrams for Bathroom Electrical Wiring with Code Requirements for most new or remodel projects.
- Basement Electrical Wiring
Basement Electrical Wiring
- Fully Explained Photos and Wiring Diagrams for Basement Electrical Wiring with Code Requirements for most new or remodel projects.
- Bedroom Electrical Wiring
Bedroom Electrical Wiring
- Fully Explained Photos and Wiring Diagrams for Bedroom Electrical Wiring with Code Requirements for most new or remodel projects.
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repair and Home Electrical Wiring:|
|« Previous||Next »|
|Replacing and Wiring Three Way Switches||3 Way Switch Wiring Variations|