Bob in Washington Lost Power to the Backside of his House
How to Troubleshoot No Power and Lost Power: The back side on my house has no power. The house has Federal circuits. I replaced all the fuses but still no power.
Troubleshooting Lost Power to Areas of the Home
Electrical Question: Hi Dave, I’ve got a good one for you. The back side on my house has no power. The house has Federal circuits. I replaced all the fuses but still no power.
- The wall outlets in the kitchen work but not the lights and switches.
- The bathroom does not have power.
- The hallway, one bedroom and one wall outlet works, but and two other outlets do not, plus a light and switch do not either.
Thank You for any information,
This electrical wiring question came from Bob, in Lakewood, Washington.
Thanks for your electrical wiring question bob.
Preparations for Troubleshooting Lost Power
Application: Troubleshooting and Repairing Outlet Problems.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrician.
Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester or Volt Ohm Meter or plug-in circuit analyzer.
Estimated Time: Depends on the age of the home and the condition of the electrical wiring and access to the circuit wiring to be inspected, evaluated and repaired.
Precaution: Identify the outlet circuit at the electric panel, turn it OFF and then Tag it with a Note before performing any wiring inspections or electrical repairs. If an outlet or the electrical wiring is found to be damaged then repairs and replacement parts should be obtained with the same voltage and amperage rating.
Notice: Burnt or damaged electrical wiring and circuit components should be replaced with new electrical materials of the same voltage and amperage rating.
How to Troubleshoot No Power and Lost Power
- Tripped GFCI Outlet
Look for a tripped GFCI Outlet or circuit breaker. A tripped GFCI will prevent power from going to other outlets and some areas of the home depending on the wiring methods. A tripped GFI Outlet may be caused by moisture related conditions. Moisture proof covers should be installed over outside receptacle outlets to prevent a tripping ground fault protected circuit.
- Damaged Wiring at an Outlet or Receptacle
Look for outlets that appear to be burnt where the plug is inserted. This is an indication that the receptacle outlet and wiring may be damaged. A burnt or damaged outlet receptacle will need to be replaced and burnt or damaged wiring and connections need to be replaced and repaired.
- Faulty Splices or Burnt Wiring Connections
Heat related damage to electrical wiring is common in older ceiling mounted light fixtures where incandescent light bulbs are used. These wiring problems are typically found in the surface style light fixtures that are mounted to the ceiling which are located in the bathroom and kitchen where two or more light bulbs are being used.
More about Troubleshooting Lost Power
- Troubleshooting Electrical Problems
How To Troubleshoot Electrical Problems with Wiring Diagrams, Photos, Questions and Answers.
Wiring Electrical Outlets for the Home
- Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Electric Circuit Listing
- The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Installing Remote Control Ceiling Fans||Litahni in Kailua Hawaii asks Why is my Electric Energy Bill So High|