Add a GFCI Outlet Circuit to a Bathroom
How should a GFCI Outlet circuit be installed for an existing bathroom?
Bathroom GFCI Outlet
Electrical Question: Jon in New Jersey asks: How should a GFCI Outlet circuit be installed for an existing bathroom?
- I have a bathroom with a GFCI outlet that feeds a vanity light and a exhaust fan/light unit.
- Currently, this bath room shares a 15 amp circuit and I want to move it to its own circuit.
- I would like to run a 12/2 wire to the GFCI, which it currently does not have. But the vanity lights and ceiling fan are run with 14/2 wire.
- Can I do this or do I need to re-wire all the fixtures with 12/2?
This electrical wiring question came from Jon, a Homeowner, in Ewing, New Jersey.
Thanks for your electrical wiring question Jon.
Bathroom GFCI Outlet Circuit
Application: Bathroom Electrical Wiring.
Skill Level: Intermediate to Advanced – Best installed by a Licensed Electrician.
Tools Required: Electricians Pouch of Hand Tools for Rough-In Wiring, Electric Drill and Auger Bits and Extension Cord.
Estimated Time: Depends on the extent of the bathroom remodel project, the type of construction and available access to the project area.
Precaution: Any existing wiring in the immediate area that may interfere with the installation of new construction materials should be identified, turned OFF and Tagged.
Notice: Modifying existing wiring or installing additional bathroom electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
Adding a Bathroom GFCI Outlet Circuit
- Bathroom GFCI Circuits in the Home
- In newer homes you will find a dedicated 120 volt 20 amp GFCI Circuit to the Bathroom Outlets. Typically the GFCI circuit is not shared with the bathroom lights or exhaust fan unless these devices are located above the shower or bathtub area.
- In older homes you may find that the GFCI outlet circuit also provides power to the vanity light and exhaust fan. This is the case with Jon, who would now like to install a separate circuit for the bathroom GFCI Outlet.
- So lets review this project:
Jon’s bathroom has a 14 amp 120 volt circuit that takes care of the bathroom GFCI outlet, the vanity light and the exhaust fan.Jon wants to add a new 20amp 120volt circuit for the bathroom outlet, but what should be done with the existing 14amp circuit?
- Installing the GFCI Outlet Circuit
The existing 14amp circuit for the vanity light and exhaust fan and light can remain the same, however the wiring to the GFCI outlet should be removed.
The new 20amp 120volt circuit may be installed and connected only to the bathroom GFCI outlet.
Now there are two circuits for the bathroom, however the wiring of each circuit is kept separate.
More about Bathroom Electrical Wiring
Wiring Electrical Outlets for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines
GFCI and GFI Wiring Diagrams
The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
Bathroom Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Bathroom Electrical Wiring with Code Requirements for most new or remodel projects.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Bathroom Electrical, Bathroom GFI Receptacle, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Wiring 3 Way Switches and Dimmer Switches||Installing a Sub Panel for a Detached Building|