50 Amp GFCI Trips When the Outlet is Installed
Why a new 50 amp GFCI breaker trips when the outlet Is installed in the box.
Wire a New Circuit for a Outlet
Electrical Question: What would cause the GFCI to trip after the outlet Is installed?
I have a new 50 amp GFCI that trips when the outlet is installed in the box.
This electrical wiring question came from Michael, a Homeowner in Toledo, Ohio.
Additional Comments: Great sight.
Thanks for your electrical wiring question Michael.
How to Troubleshoot a Tripping GFCI Breaker
Application: Wire a New Outlet and GFCI Breaker.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor, or Certified Electrician.
Electrical Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester, and appropriate Safety Gear.
Estimated Time: Depends on the personal level experience, ability to work with tools, install electrical circuit wiring, and the available access to the project area.
Electrical Safety: Identify the electrical power source to the Outlet, turn it OFF and Tag with a Note before working with the electrical wiring.
Electrical Wiring Parts and Materials: Electrical parts and materials for the Outlet should be approved for the specific project and compliant with local and national electrical codes.
Electrical Codes and Inspections: Installing or changing home electrical wiring should be done according to local and national electrical codes as adopted in Toledo , Ohio. A permit and inspections may also be required.
See more about Home Wiring for Ohio
Problem when Wiring a Outlet in a Basement
This electrical wiring project is about a 50Amp Breaker and Outlet in the Basement of a Old Home.
GFCI Breaker Trips after Installing the Outlet
- Michael, From what you have described, the first thing to check is to make sure the connections have been made to the right terminals on the outlet.
- Next, make sure the wiring connections to the outlet are secure and that no part of the wiring or terminal connections come into contact with any part of the box.
- Also, make sure the mounting screws of the outlet are not hitting or penetrating any electrical wires inside the box, and there are no pinched wires between the outlet and the box.
- When the breaker trips off, there may be signs of arcing, so look for this which will give you a clear indication of where the problem is.
More about Wiring a New Outlet Circuit
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Electrical Junction Boxes for Home Wiring
Understanding electrical junction boxes and what they are used for. Home electrical wiring is the process of installing electrical wire to a location that will serve electrical devices or an appliance. One very important component is the box where the wire will be installed. The type and size of the home wiring electrical boxes will depend upon the circuit size, application and its location.
Wiring Electrical Outlets for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Basement Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Basement Electrical Wiring with Code Requirements for most new or remodel projects.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|More articles about Electrical Wiring, GFCI, Hot Tub GFCI Breaker and Home Electrical Wiring:|
|« Previous||Next »|
|How to Locate an Electrical Wiring Problem||Someone is Spying On Me, How Can I Detect these Spy Devices?|