Filed under Electrical Wiring
Why Air Conditioners Trip Circuit Breakers
By Dave Rongey - Summary:|
Air Conditioner Units and Tripping Circuit Breakers: The circuit that an air conditioner is connected to may be shared with other outlets so the circuit is becoming overloaded, here is how to solve this problem.
Air Conditioner Electric Circuit
- We all have portable AC units in our room for that, but whenever I try to turn on my portable AC, the window AC also goes off after a minute or so, we noticed that the circuit breaker keeps popping/tripping so we go back and reset it. However, only the window AC automatically turns back on, while my portable AC does not. If I try to turn it back on, it runs for a minute again and then shuts off, popping the circuit breaker switch again. My roommate’s portable AC is able to run at the same time as the window AC, and the other roommate’s portable AC is on a different circuit (fairly certain since she never seems to have problems with it shutting off), so right now I’m the only one without AC and it is sweltering in this NYC heat.
- The switch that keeps popping says it has 15 amps on it. The window AC is 11,000 BTU and my portable AC is 10,000. There’s a bunch of other 15 amps switches and 2 other longer/bigger looking switches that say 40 amps on them. Is it overloading on that one 15 amp circuit? Yesterday, I tried turning off the window AC to turn mine on, but it still tripped the circuit.
- However, tonight I turned my portable AC on with the window AC running and it is working. My roommate’s portable AC is off though so I think maybe that all three AC units can’t run at the same time?
- I contacted my landlord who said he would send his repairman over to look at it soon but he’s slow with these things so I don’t know how soon that will be. What exactly can be done in this situation… is it possible to somehow rewire the circuit so that one of our AC units can go onto a different circuit and everyone can have their AC units on?
This electrical question came from: Stacy, from New York, New York.
Thanks for your electrical wiring question Stacy.
Air Conditioner Tripping the Electrical Circuit
Portable Air Conditioner Units and Electrical Circuit Requirements
- As described in this question, the circuits that the air conditioners are connected to are shared circuits that are becoming overloaded which is causing them to trip off.
- This typically happens when a portable or window air conditioner is plugged into an outlet circuit that may be shared with other outlets, so the circuit can become overloaded and cause the circuit to trip off.
- A dedicated circuit should be installed for each window air conditioner which will prevent the room outlets from becoming overloaded.
More about Electrical Wiring
Electrical Circuit Wiring
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Rewiring a Home
Rewiring a Home
Great ideas for home electrical rewiring that will add value to your home and bring it up to the current safety and energy efficient electrical codes.
Learn How to Wire it Right!
Complete Guide to Home Electrical Wiring
Perfect for Homeowners, Students,
Handyman, Handywomen, and Electricians
Wiring GFCI Outlets
Wiring Home Electrical Circuits
120 Volt and 240 Volt Outlet Circuits
Wiring 3-Wire and 4-Wire Electric Range
Wiring 3-Wire and 4-Wire Dryer Cord and Dryer Outlet
Troubleshooting and Repair Electrical Wiring
Wiring Methods for Upgrading Electrical Wiring
Electrical Codes for Home Electrical Wiring
....and much more.
» Click here to learn more about Home Electrical Wiring «
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all projects.
|« Electric Well Pump Circuits||Installing Three Way Dimmer Light Switches »|