Wiring a 4-Wire Range Cord to a 3-Wire Outlet
Can I install a 3 wire cord on a new stove and strap the neutral and ground on the stove terminals? Ground and Neutral Wiring for a 220 Volt Range.
Electrical Wiring for a 220 Volt Range
Electrical Question: Can I install a 3 wire cord on a new stove and strap the neutral and ground on the stove terminals?
- I have an older house with an old 3 wire range.
- The receptacle is wired with 2 hot wires and a un-insulated twisted aluminum conductor for ground.
- The replacement stove has a 4 wire, 2 hots, neutral and ground.
- The new stove uses the the neutral for all the 110v circuits.
- Is it legal to install a 3 wire cord on the new stove and strap the neutral and ground on the stove terminals?
- This would make the ground at the receptacle a current carrier.
Thanks for your electrical question Jeffrey.
Wiring a 220Volt or 240Volt Range Cord
Application: Wiring a 220 Volt or 240 Range Cord.
Skill Level: Beginner to Intermediate. This electrical wiring project is best performed by a Licensed Electrical Contractor.
Tools Required: Basic Electricians Pouch Hand Tools and a Voltage Tester.
Estimated Time: Depends on personal level experience, ability to work with tools and the available access to the range cord electrical connection box.
Precaution: Identify the range circuit, turn it OFF and Tag it with a Note before working with the range cord wiring.
Ground and Neutral Wiring for a 220 Volt Range
Fully explained wiring instructions complete with a picture series of an installation and wiring diagrams can be found here in the Kitchen Range area here in this website. Just click the Wiring a Kitchen Range Cord link found below:
More about Wiring a Range Cord
For more information about 220 Volt Wiring Diagram
220 Volt Wiring Diagram
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 220 Volt Wiring, Electrical and Home Electrical Wiring:|
|« Previous||Next »|
|Testing 220 Volts||Why do my outlets have 120 volts and nothing works?|