Wiring a 240Volt Air Compressor
I am wiring a new air compressor. It is 240volt, 28 amps, 7.5 hp, single phase. Is #6 wire big enough?
240Volt Air Compressor
Electrical Question: I am wiring a new air compressor. It is 240volt, 28 amps, 7.5 hp, single phase. Is #6 wire big enough?
I am wiring a new air compressor. It is 240v, 28 amps, 7.5 hp, single phase. It has a magnetic starter and the motor has it’s own overload protection.
The manufacturer recommends an 80 amp breaker because of the initial startup draw. I am using a 10 hp non fused disconnect to turn it on and off. It is only 10 feet from the breaker panel and wires will be run in conduit.
My question is this, is #6 wire big enough ?
I seem to be getting differing opinions. some say I need #3 because of the 80 amp breaker. Some say because it is wiring to a motor only, it can be much smaller. Even down to #8
Your help would be much appreciated.
This electrical wiring question came from Jeff, a Handyman in Sandwich, Illinois.
Additional Comments: First time visiting – hopefully helpful.
Thanks for your electrical wiring question Jeff.
How to Wire a 240Volt Air Compressor
Application: Wire a New Circuit for an Air Compressor.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor, or Certified Electrician.
Electrical Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester, and appropriate Safety Gear.
Estimated Time: Depends on the personal level experience, ability to work with tools, install electrical circuit wiring, and the available access to the project area.
Electrical Safety: Identify the electrical power source to the Air Compressor, turn it OFF and Tag with a Note before working with the electrical wiring.
Electrical Wiring Parts and Materials: Electrical parts and materials for the Air Compressor should be approved for the specific project and compliant with local and national electrical codes.
Electrical Codes and Inspections: Installing or changing home electrical wiring should be done according to local and national electrical codes as adopted in Sandwich, Illinois. A permit and inspections may also be required.
Wire Size for a 7 1/2 HP 240Volt Air Compressor
Jeff, from what you have described I have come up with the following:
Based upon a 7 1/2 HP Motor, 240Volt, Single Phase:
Full Load Current: 40 Amps.
Minimum Copper Wire Size: #6 – (Wire Types THW, THHN, THWN are Rated at 65 Amps).
Thermal Magnetic Trip Rating: 80 Amps.
Time Delay Fuse Rating: 60 Amps.
You need to keep in mind that the Starting Amperage, and the Running Amperage are the factors.
The Magnetic starter and the Thermal Magnetic Overload Protection help to protect the motor when it is starting, therefore the correct wire size is important.
The Running Amperage is taken into consideration for the wire size and the circuit breaker size.
Most circuit breakers are designed to take the in-rush of starting current that lasts only a few seconds, so generally the circuit breaker should not trip off when the motor is starting as long as everything has been sized properly.
The following articles that may assist you as well:
More about Wire a New Circuit a Air Compressor
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Wiring 240 Volt Electrical Outlet
Home electrical wiring includes 110 volt outlets and 240 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.
Work Shop Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Workshop Electrical Wiring with Code Requirements for most new or remodel projects.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|« Lightning Strikes and Electrical System Protection||How to Troubleshoot Incorrect Voltage for a Stove »|