Why Circuit Breakers Trip Off and What To Do Next
Mona from Daly City, California asks: What Causes a Circuit Breaker to Trip Off? The Most Common Problems that Cause a Tripping Circuit Breaker.
Circuit Breaker Problems
Electrical Question: Are tripping circuit breakers dangerous for computers and electronic devices?
- In my kitchen, while using microwave and toaster oven at same time trips the breaker. Also when using my hairdryer in the bathroom and the microwave or other appliance the circuit trips off.
- This also shuts down the TV, two DVD recorders and probably the Mac Book Pro but since it has battery back-up it stays on. Is this dangerous for his Mac.
- The property owner is allowing some guy to fix the problem by changing a 20 amp circuit breaker to a 30 amp circuit breaker. This must be wrong.
- I didn’t think the kitchen should be connected to any other place in house.
- I know some things in kitchen should have their own circuit breaker.
Help, I need to show how dangerous this could be if the owner proceeds as planned.
This electrical question came from: Mona, from Daly City, California.
See more about Electrical Wiring in California
Additional Comments: Awesome website, Thank you.
Thanks for your electrical question Mona.
Why Circuit Breakers Trip Off
Application: Identifying Electrical Circuit Problems.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor or Certified Electrician.
Tools Required: Electricians Pouch of Hand Tools for Rough-In Wiring, Electric Drill and Auger Bits and Extension Cord. All safety measures must be taken for your protection while working around environmental and construction hazards and when working with all types of tools.
Estimated Time: Depends on the extent of the project, the type of construction and available access to the project area.
Precaution: Any existing wiring in the project area should be identified, turned OFF and Tagged. Old electrical wiring that will be replaced with new electrical wiring should be removed.
Notice: Installing additional electrical wiring should be done according to local and national electrical codes with a permit and be inspected.
The Purpose of a Circuit Breaker
Circuit breakers prevent electrical overload that could damage electrical wiring components which could result in a fire.
Troubleshooting a Circuit Breaker Problem
- This question describes a serious electrical wiring condition and the wrong solution to the problem.
- As described, there is a overload condition with the electrical system of the home because dedicated circuits are not installed according to current codes.
- As Mona has stated, the kitchen should have its own dedicated circuits, in fact there should be at least two 20 amp circuits for the kitchen counter top receptacles which should be protected by GFCI.
- When a circuit becomes overload and starts to trip the breaker off this is an indication that the electrical system should be evaluated and additional circuits should be installed to bring the home up to the current code requirements.
The Most Common Problems that Cause a Tripping Circuit Breaker
Question about a Circuit Breaker Problem: My son has a circuit breaker that just started to trip pretty much as soon as he resets it.
- I am trying to help him fix the problem. I have a good tester but am not sure to how to determine the probable cause without simply replacing stuff and sometimes that can get expensive besides time consuming. If you have any suggestions would appreciate a plan of action.
This electrical wiring question came from Jim, a Handyman, in Hurst, Texas.
See more about Home Wiring for Texas
IMPORTANT: If a circuit breaker is tripping off it may not be a problem with the breaker itself.
- Improper Circuit Design
If a circuit is not designed properly the breaker may trip off due to an overloaded condition.
- Improper Circuit Installation
If the circuit wiring and components are not installed correctly there could be a direct short in the circuit which could cause the breaker to trip off.
- Large Equipment Can Cause Overload
Equipment that requires a lot of power may overload the circuit and cause it to trip off, this is why some equipment require a separate dedicated circuit to be installed.
- A Device Connected to the Circuit Has a Problem
Devices could cause a circuit to trip off due to many problems including
- Damaged electrical receptacle outlet.
- Damaged electric cord.
- Damaged internal electric component.
- Bad motor bearings or worn out parts.
What to do about a Tripping Circuit Breaker
Now that we have discussed the possible problems associated with a tripping circuit breaker the following should be considered for possible solutions:
- Circuit Problem
- The circuit should be evaluated to make sure it is sized properly and installed according to applicable codes.
- In some cases circuit wiring may need to be replaced, or an additional circuit may be required.
- Device or Equipment Problem
- Faulty items should be disconnected from the circuit and repaired or replaced as needed.
- Faulty Circuit Breaker
- If a circuit breaker is found to be faulty then it should be replaced.
Selecting the Right Circuit Breaker
- A circuit breaker should only be replaced by the same type and amperage breaker which is properly size for the circuit wire size.
- A circuit breaker should NEVER be replaced with one that is of a larger amperage rating because this could allow the electrical wiring to become overloaded which will over heat the wiring and could cause a fire.
Important: A tripping circuit breaker may be an indication that additional circuits may be required.
More about Electrical Wiring and Circuit Breakers
Electrical Circuit Wiring
- This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuit Breakers
- A guide to home electrical circuit breakers and how they work to protect your electrical wiring.
- When properly installed, your home electrical wiring is protected by a circuit protection device.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repair, Electrical Troubleshooting, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|I accidentally cut into a wire is there anything I can do?||Wiring for GFCI Outlets|