Why a New Hot Tub May Not Work Right
Why is my new hot tub not working right? Why a Hot Tub Stops Working and the Breaker Does Not Trip.
New Hot Tub Problem
Electrical Question: Why is my new hot tub not working right?
My electrical wiring question involves an electrical problem with a GFCI breaker for a hot tub.
- I have 130′ run of (3) 6 AWG wires and (1) 8 AWG ground wire from a main panel 50 amp standard Breaker (100amp total service) to a spa sub panel using 1″ PVC sch 40 grey conduit with a 50amp GFIC breaker in the spa sub panel box.
- There are no other breakers in the box or anything else on the circuit. The run to the spa is about 15′ and has the same wire configuration in a 3/4″ combination liquid tight flex conduit to internal 1″ solid conduit in the spa itself. Everything seems right to me however, when running the spa jets (2 pumps) for an hour or so, the Breaker in the sub panel gets hot and the spa stops running.
- The circuit breaker does not trip but when it gets too hot and the spa does not work, and the test button does not function properly. After I shut it off and it cools down everything works fine again until the GFCI breaker gets hot again.
- The wiring is about 10 years old and was installed prior to me purchasing the house but the spa is brand new and was installed just last Friday. The Spa manual requires a min. 40 amp 240 volt service. When I test the sub panel connections I get good 120Volt on both L1 and L2. However at the spa after the GFCI breaker the voltage at L1 is 125 and at L2 115. not sure why. Could this be the problem?
- The only other thing I can think of is that the original wiring run from main panel to sub panel is faulty somewhere in the conduit. If this was the case could it cause this problem? I don’t want to run new wire if I don’t have to. Is there a way of testing that run of wire to find faults? Is there any other reason you think this could be happening?
This electrical wiring question came from Robert, a Handyman in California.
Thanks for your electrical wiring question Robert.
Hot Tub Problem
Application: Electrical Problem with a Hot Tub GFCI Breaker.
Skill Level: Intermediate to Advanced – Best performed by a Licensed Electrical Contractor, or Certified Electrician.
Electrical Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester, and appropriate Safety Gear.
Estimated Time: Depends on the personal level experience, ability to work with tools, install electrical circuit wiring, and the available access to the project area.
Electrical Safety: Identify the electrical power source to the GFCI Breaker, turn it OFF and Tag with a Note before working with the electrical wiring.
Electrical Wiring Parts and Materials: Electrical parts and materials for the GFCI Breaker should be approved for the specific project and compliant with local and national electrical codes.
Electrical Codes and Inspections: Installing or changing home electrical wiring should be done according to local and national electrical codes as adopted in California. A permit and inspections may also be required.
Hot Tub Stops Working and the Breaker Does Not Trip
Here are my thoughts and questions for you to consider regarding the problem you are experiencing with your hot tub:
Circuit Requirements for the Hot Tub
How big was the previous hot tub electrical circuit requirements compared to the new hot tub?
I am guessing that the new hot tub has a higher amperage requirement compared to the previous one.
Length of the Circuit Wires
The length of the wire run is of concern to me, especially if any of the circuit conductors are aluminum wire.
NOTE: Most hot tubs require copper wire only due to the high amperage requirements.
Testing the Voltage
A voltage test should be taken while the hot tub is running to see if there is a voltage drop condition. A voltage reading while the hot tub is not running will only reveal the voltage without a load, but once the hot tub is on along with all of the components, especially the heater, then you will get a true understanding of what the circuit voltage condition really is.
Hot Tub Problem
It is important to know that this type of a problem is typically not a fault of the hot tub, it is simply the wrong electrical circuit wire size based on the total length of the wire and the amperage requirements of the hot tub. The longer the length of wire, the more voltage drop will occur.
Voltage Drop Condition
If it is found that there is a voltage drop condition then the wiring will need to be replaced with the next size larger, or if the circuit wiring is aluminum then it will need to be replaced with copper wire.
Low Voltage Causes Over Heating
When there is a voltage drop condition it is common that the circuit components will overheat, and eventually motors will burn out and other damage will occur to the electrical components due to excessive overheating.
Circuit Wiring as Required
In addition, make sure the circuit wiring is correct. Specifically, if the hot tub requires a separate neutral and a separate ground wire, along with the power conductors then the circuit must match the requirements, and that the wiring has been configured and connected to the hot tub correctly.
More about Hot Tub Electrical Wiring and GFCI Breakers
House Wiring Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Spa Tub Circuit Wiring
Electrical Codes and details for Spa and Hot Tub electrical wiring. Essentials for your hot tub installation, including the required gfci ground fault protection and circuit wire size.
GFCI and GFI Wiring Diagrams
The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
Electrical Grounding Methods and Requirements
Listing of electrical codes for grounding with examples of electrical grounding codes for home electrical wiring.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about GFCI Circuit Breaker, Hot Tub, Hot Tub Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Recessed Can Lights Last Only a Few Months||Ceiling Fan Works but Not the Light|