Understanding Multi-Wire Circuits
Circuits four and eight share the same neutral, is this correct?
Multi-Wire Circuits and Shared Neutrals
Question: Circuits four and eight share the same neutral, is this correct?
This electrical question came from: Marvin , a Student from San Diego, California.
See more about Home Wiring for California
Thanks for your electrical question Marvin.
Multi-Wire Circuit Wiring
Marvin, if the circuit breakers are full size then no, this is not correct. A multi-wire circuit that shares the same neutral must have each of the two circuits on separate buses, and the circuit breakers must be have their handles tied. This will ensure a balanced load on the neutral.
The Following links will assist you with your electrical question:
Electric Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
For more information about 220 Volt Wiring Diagram
220 Volt Wiring Diagram
Wiring 220 Volt Electrical Outlet
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.
This link is helpful as a Student
Electrical Code Articles
|« Replacing a Faulty Dimmer Switch||Basement Circuits and Electrical Wiring »|
Browse other questions in the following categories:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.