Three Way Switch Wiring Diagrams
The Process for Wiring Three Way Switches – Here is a a comprehensive,step-by-step guide designed to walk you through the identification and wiring of your 3-way switches.
Wiring for Three Way Switches
Electrical Question: I have a set of switches at the top of my steps leading to the basement.
SWITCH BOX 1.
One switch controls a fixture at the top of the steps(single pole). The other controls several high-hats in the basement(three-way). In box 1 there is one 3wire and a pair of 2wire. Down in the basement is another set of switches.
SWITCH BOX 2.
One switch controls the high-hats(the other three way) and the second switch controls a fixture in the garage(single pole) In box 2 there is a set of 3wire and one 2wire.
I have determined that in box 2 one 3wire is my feed and the other goes to the top of the steps. the 2wire in box 2 also goes up to the top of the steps. I have also determined which wire in box 1 feeds the fixture at the top of the steps.
I can not get the 3way switches to work. Can you help?
This electrical wiring question came from: Andrew, a Contractor from Wilmington, Delaware.
See more about Home Wiring for Delaware
Dave ‘s Reply:
Thanks for your electrical wiring question Andrew.
The Process for Wiring Three Way Switches
Skill Level: Beginner to Intermediate.
Tools Required: Basic Electricians Pouch Hand Tools and Voltage Tester.
Estimated Time: Depends on personal level experience and ability to work with tools.
Here is a a comprehensive,step-by-step guide designed to walk you through the identification and wiring of your 3-way switches.
For more information about 3 Way Switch Diagram
3 Way Switch Diagram
3 Way Switch Diagram
In response to the requests for this information, I have developed a comprehensive,step-by-step guide designed to walk you through the identification and wiring of your 3-way switches.
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about 3-Way Switches, Electrical Repair, Electrical Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|Locating and Installing Pot Lights||Hairdryer Outlet and GFI Safety Requirement|