Replacing Pushmatic Circuit Breakers
One and Two Pole Pushmatic Circuit Breakers: I need to replace Pushmatic UBIP230 Circuit Breakers.
Pushmatic Circuit Breakers
Electrical Question:I need to replace Pushmatic UBIP230 Circuit Breakers.
- We have a house built in 1951 with the old style Pushmatic circuit breakers.
- We are needing to replace the 220 dryer breaker. It is currently set up with two 1 pole 30amp breakers that have a steel push bar on them so both breakers can be reset with one push.
- Ive been told that they can be replaced with a single 2 pole 30amp breaker and the pics Ive seen looks as though it would be a good fit. the part numbers i have found are UBIP230 for the 2 pole, and UBIP130 for the single pole.
- Just want a second opinion before I do anything because from what Ive seen these are expensive breakers and if i can buy 1 instead of two for the same price that would help! whats your opinion?
Any advice would help!
This electrical question came from: Hugh, from Wichita, Kansas.
Thanks for your electrical question Hugh
Installing Pushmatic Circuit Breakers
Application: Installing or Replacing a Pushmatic Circuit Breaker.
Skill Level: Advanced – Licensed Electrical Contractor, Not Recommended for Homeowners.
Tools Required: Electricians pouch of hand tools, voltage tester and protective safety gear.
Estimated Time: Depends on the make and model of the panel and the condition of the existing electrical circuit breakers and wiring methods.
Precaution: For safety the main circuit breaker should be turned off or any other disconnect means that would deenergize the panel before replacing a circuit breaker, however turning off the main circuit breaker may not deenergize all of the areas of the panel components and wiring. This is an extensive project that requires experience and should be performed by a Licensed Electrical Contractor.
Notice: Making changes to electrical panel or electric circuits should be done according to local and national electrical codes with a permit and be inspected
1 Pole and 2 Pole Pushmatic Circuit Breakers
Installing a 2 Pole Pushmatic breaker or an Approved Tie bar
- When purchasing a 240 volt circuit breaker it is best to purchase one 2-pole circuit breaker instead of two 1-pole circuit breakers.
- Tie bars can be installed to create a 2-pole breaker out of two 1-pole circuit breakers if a 2-pole circuit breaker cannot be located, just be sure the tie bar is UL approved for the application.
More about Circuit Breakers
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Wiring 220 Volt Electrical Outlet
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how electrical outlets for the home are wired.
3-Wire and 4-Wire Configurations for Clothes Dryers
See an electric dryer installation with a typical 220 Volt electric power cord wiring system. You may find yourself with either a 3-wire or 4-wire electric dryer, or a 3-wire or 4-wire outlet. Lets look a how the electric dryer is wired and what to do if your cord does not match the plug.
|« Wiring Receptacles and a Light Switch||Wiring a 30 Amp Outlet for a Motor Home »|
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.