Neutral and Ground Wires in a Sub Panel
How to Configure the Neutral and Ground Wires in a Sub Panel – In a sub-panel the Neutral Wires must be separated from the Ground Wires and may not be terminated on the same buss, regardless if the ground wire is insulated or not.
Separation of Neutral and Ground Wires in Sub Panels
Electrical Question: We are considering buying a manufactured cabin that has a Jacuzzi tub. The neutrals and grounds are tied together on the same bus in the sub panel. One home inspector said they need to be separated, the other said they are fine since they are both insulated and are grounded at the main panel. Which is correct?
This electrical question came from: Dan, from Big Bear City, California
Thanks for your electrical question Dan
How to Configure the Neutral and Ground Wires in a Sub Panel
In a sub-panel the Neutral Wires must be separated from the Ground Wires and may not be terminated on the same buss, regardless if the ground wire is insulated or not. This is especially true for manufactured homes and mobile homes where a 4-wire system whereby the neutral and ground wire separation is essential.
House Wiring Circuits and Circuit Breakers
A typical 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Electrical Panel Circuit Listing
Jacuzzi Tub Circuit Wiring
Electrical Codes and details for Spa and Hot Tub electrical wiring. Essentials for your hot tub installation, including the required GFCI ground fault protection and circuit wire size.
|« Don’t Burn Your House Down – The Key to Safe Extension Cords||Why Home Lighting May Stop Working »|
Browse other questions in the following categories:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.