Is Your 240 Volt Outlet Safe
Examining a 240 Volt Circuit and the Electrical Wiring Components for Safety – The wire gauge of the circuit should be verified. If it is found that the circuit wire AWG gauge is #12 then the circuit breaker amperage size could be increased to be a 20 amp 2 pole circuit breaker.
Examining 240 Volt Circuit Components
Electrical Question: I have a dual 15 amp 2 pole circuit breaker that outputs 240V to a single 240V 20 amp outlet.
- Is this acceptable?
- It was installed when the house was built 20 years ago.
- I’m concerned about the safety of the electrical wiring.
This electrical wiring question came from: Jeff, a Handyman from Hudson, New Hampshire.
See more about Home Wiring for New Hampshire
Thanks for your electrical wiring question Jeff.
Examining 240 Volt Circuit Components and Electrical Wiring for Safety
- Because the 240 volt receptacle outlet is rated at for 20 amps then the circuit wiring should be 20 amps.
- The wire gauge of the circuit should be verified. If it is found that the circuit wire AWG gauge is #12 then the circuit breaker amperage size could be increased to be a 20 amp 2 pole circuit breaker.
- If the AWG wire gauge is found to be #14 then the 20 amp 240 volt receptacle outlet should be replaced by a 15 amp 240 volt receptacle outlet and the appropriate cover.
- You may see that there are a few different types of 240 volt receptacle outlets available, such as straight blade and twist lock, 3-wire and 4-wire configurations.
- The correct receptacle outlet should be selected to be compatible with the 240 volt circuit and the application or 240 volt equipment that will the receptacle outlet will be used for.
The Following Resources will assist you with your electrical wiring question:
Wiring Electrical Outlet for the Home
Home electrical wiring includes 110 volt outlets and 220 volt outlets and receptacles which are common place in every home. See how wiring electrical outlets for the home are done.
Home Electrical Circuit Listing
The size of the home electrical service panel is designed by calculating the square footage of the home and factoring in the code requirements for the electrical circuits that are required.
Guide to Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Electrical Code and Protecting NM Cable||How do I install a wire from my electrical panel for light switches? »|