Installing Electrical Power to a Garage
How should I Wire a GFCI Circuit Breaker for my garage electric panel? Garage Electrical Wiring, How to Wire a GFCI Circuit Breaker.
Electrical Question: How should I Wire a GFCI Circuit Breaker for my Garage Electric Panel?
I need to fix some electrical problems with my garage wiring.
- I have had a garage built in the garden. It has a small panel board that feeds various circuits with 15A breakers.
- The feed is from an existing panel board in the house. The feeder breaker to the garage panel board is 40A with an integrated Ground Fault Interrupter and Earth Leakage Protector.
- The problem I have, is that when I switch OFF the garage fluorescent lights, the 40A GFI breaker in the house panel board trips. It doesn’t trip the 15A breaker in the garage panel.
- Why would this switching OFF of the lights trip the main GFI breaker? Should I run the neutral directly to the neutral bar & bypass the GFI in the 40A breaker.
Your comments would be much appreciated.
This electrical question came from: John, from Vancouver, Canada.
Thanks for your electrical question John.
How to Fix Garage Electrical Wiring Problems
Application: Troubleshooting and Repairing Garage Electrical Wiring Problems.
Skill Level: Intermediate to Advanced. This electrical wiring project is best performed by a Licensed Electrical Contractor or Certified Electrician.
Tools Required: Basic Electricians Pouch Hand Tools, Voltage Tester or Volt Ohm Meter or plug-in circuit analyzer.
Estimated Time: Depends on the age of the home and the condition of the electrical wiring and access to the circuit wiring to be inspected, evaluated and repaired.
Precaution: Identify the circuit at the electric panel, turn it OFF and then Tag it with a Note before performing any wiring inspections or electrical repairs.
Troubleshooting a Garage Electrical Wiring Problem
How to Wire a GFCI Circuit Breaker
- The neutral wire of the circuit to be protected by ground fault must be attached to the GFCI circuit breaker neutral wire terminal,. The neutral lead wire of the GFCI breaker attaches to the neutral bar of the panel.
Garage Electrical Wiring
- If the garage light fixture is tripping the GFCI circuit breaker then make sure the light fixture is properly grounded and that the switch is a good quality switch.
- The neutral wire of the circuit must be attached to the GFCI circuit breaker, then the neutral lead wire of the GFCI breaker attaches to the neutral bar in the panel.
- Keep in mind that light fixtures that are over 7 feet high, or are nor accessible, are not required by NEC Code to be GFCI protected, however the accessible outlets are.
- The main circuit to the garage is not required to be on GFCI circuit breaker either unless the feeder cable is UF or Direct Burial cable and the depth is not per code.
- Check with the local electrical codes which may required the garage feeder to be protected by GFCI, according to the CEC Canadian Electrical Code or NEC depending on your specific location.
See more about Garage Electrical Wiring
How to Install Garage Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Garage Electrical Wiring with Code Requirements for most new or remodel projects.
Basic House Wiring Circuits
House Wiring GFCI Circuits and Circuit Breakers
This article looks at common 120 volt and 240 volt house wiring circuits and the circuit breakers that are installed identifying the types and amperage sizes used in most homes.
Home Electrical Circuit Breakers
A guide to home electrical circuit breakers and how they work to protect your electrical wiring. When properly installed, your home electrical wiring is protected by a circuit protection device.
GFCI and GFI Wiring Diagrams
The features and benefits of GFCI outlets and receptacles will give you a clear understanding of the importance why these safety devices are required by code to help protect you and your family against accidental electrical shock hazards.
Wiring a GFCI Outlet
This list of articles will help you learn about the features and benefits provided by GFI and GFCI Receptacles and how they are wired.
Using Testers to Identify Electrical Problems
Testers to Help Solve Electrical Problems
Troubleshooting Electrical Wiring
The following may also be helpful for you:
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Electrical Repair, Electrical Wiring, Garage Wiring and Home Electrical Wiring:|
|« Previous||Next »|
|How to Install a Time Switch for an Exhaust Fan||Replacing Aluminum Electrical Wiring with Copper|