Installing Home Electrical Wiring
Is it permissible to install Romex electrical wire through stud bore hole’s (inside the wall) located above doors and windows…
Electrical Question from Curtis about Installing Home Electrical Wiring
Background: Curtis, a Homeowner from State College, Pennsylvania
Question: Is it permissible to run/install Romex electrical wire through stud bore hole’s (inside the wall) located above doors and windows?
Additional Comments: So far so good.
Thanks for your electrical question Curtis.
Yes – just make sure the holes are drilled in the center of the studs and use safety plates where the wire may be vulnerable to nails or screw when applying the finished wall covering materials.
The Following links will assist you with your electrical question:
For more information about Home Wiring
Home Wiring Diagrams
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|« Calculate Electrical Circuits for Lights and Outlets||Electrical Repair for an Outlet Circuit »|