Installing a Sub Panel for a Detached Building
Do I need to run a ground wire for a 200 amp sub panel that is 200 feet away from the main panel? Grounding a Remote Sub Panel at a Detached Building.
Grounding a Sub Panel at a Detached Building
Electrical Question #1: Do I need to run a ground wire for a 200 amp sub panel that is 200 feet away from the main panel?
- My question is about Grounding a Sub-Panel: I am installing a 200 amp sub panel to an existing structure that is 200 plus feet away from the main panel.
- The structure has a uffer ground rod installed, (20 foot rebar tied to the main slab / footing rebar) and I can install secondary grounded rod as well outside.
- Question: can the structure stand alone with its own grounding system? or do I need to run a ground wire back to the main panel.
- I am Using 2/0 copper wire in PVC conduit buried to get from the main panel to the structure.
This electrical wiring question came from Dennis, in Placereville, California.
Electrical Question #2:
What is the proper way to run an electrical supply to a sub panel in a barn or outbuilding?
This electrical wiring question came from Chris, a Handyman in Johns Creek, Georgia.
Thank you for your electrical wiring questions.
Grounding a Remote Sub Panel at a Detached Building
Application: Installing a Sub Panel for a Separate Building.
Skill Level: Advanced – Licensed Electrical Contractor – Not Recommended for Homeowners.
Tools Required: Electricians pouch of hand tools and the various power tools necessary for the specific method of electrical service installation.
Estimated Time: Depends on the type of panel, the location, and available access to the project area.
Precaution: This is an extensive project. Working in an electric panel has possible arc flash hazards and should be performed by a Licensed Electrical Contractor.
Notice: Installing an Electrical Service Panel must be done according to local and national electrical codes with a permit and be inspected.
Grounding a Sub Panel 200 Feet from the Main Panel
Electrical codes and information that should be considered when installing an electrical sub panel at a remote building.
- The Grounding System for a Separate Structure
- A ground wire is not required in the conduit that is feeding power to the panel at the separate structure.
- A GES, Grounding Electrode System must be provided at the separate structure for the sub panel.
- Grounding electrode conductors for the remote panel must be sized per NEC Table 250.66
- As per NEC Article 250.32-B-1 – Do Not install a bonding jumper to the neutral bar. Make sure to isolate the grounds and neutrals separately.
- NEC Article 225.31 – A main breaker must be installed if there are more than six circuit breakers in the sub panel.
More about Installing a Sub Panel
Electrical Wire for the Home
Complete listing of electrical wire types and parts used for home projects with electrical code information serves as selection guidelines.
Electrical Code Articles for Home Wiring
Electrical Code Directory covering basic electrical codes for grounding, panels and services, and underground wiring.
Circuit Breaker Panel
Electrician Explains Circuit Breaker Panels Complete with Photos. The home circuit breaker panel contains several circuit breakers that are carefully installed by experienced electricians and electrical contractors.
How to Install and Wire a Sub-Panel
How to Install and Wire a Sub-Panel – Photos and Explanation Describes the Right Way and the Wrong Way.
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
|« Installing LED Under Cabinet Puck Lights||About Light Fixtures and No Ground Wire »|