How Do I Wire A Potentiometer To My Pump VFD?
The connections for a potentiometer are as follows…
Electrical Question from Eric about Electrical Wiring for a Variable Frequency Drive
Background: Eric, a Handyman from Delta, CO
Question: I have an irrigation pump that is controlled by a VFD. The VFD output can be controlled by a remote potentiometer which I am attempting to install. I have no instructions for the potentiometer. It is correctly sized for this application. The potentiometer has three tabs for electrical connections. The VFD has three terminals for the potentiometer to hook to. They are labeled L (analog ground for excitation), H (DC 10V reference) and O (voltage input for the signal). How do I determine which tab on the potentiometer corresponds with each VFD terminal?
Thanks for your electrical question Eric.
The Make and Model/Part Numbers of both the VFD and the Remote Potentiometer: VFD – Hitachi L300P450LFU2, Potentiometer – Alpha B1K
Looking at the pot with the ShaftÂ Pointing Towards You the Tabs would be 1 -2 -3 , Left to Right, Tabs Pointing Down.
Tab 1 is GroundÂ – VFD – L Analog Ground
Tab 3 is Voltage Input – VFD H DC 10V
This answer is limited to the above mentioned VFD only. The potentiometer connections are standard.
The Following links will assist you with your electrical question:
For more information about Electrical Wiring
This link is helpful as a Handyman
Make sure not to miss these Resources for: How-To-Videos
Be Careful and Be Safe – Never Work on Energized Circuits!
For Best Results Consult a Licensed Electrical Contractor.
Locate An Electrical Contractor in Your Area
Be Careful and Be Safe - Never Work on Energized Circuits!
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wiring!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester, [amazon.com], I use for the detection of Standard Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
|« Does it Matter Where the Power Enters 4-Way Switch Wiring?||My Apex Television is Beeping – Is It a Power Problem? »|