Electrical Wiring for a Bath Exhaust Fan
How to Install Bathroom Exhaust Fan Electrical Wiring – Fully Explained Photos and Wiring Diagrams for Bathroom Electrical Wiring with Code Requirements for most new or remodel projects.
Electrical Wiring for a Bath Exhaust Fan
I am installing a Hunter model number 83003 exhaust fan, light, night-light combo.
There is no original wiring as I am turning a bedroom into a bathroom and gutted the entire room.
The fixture has one two pin connector consisting of one black wire and one white wire for the fan.
It has one 3 pin connector consisting of one white wire, one black wire for the light, one red wire (night-light).
I ran 12-2nmb from the light switch box to the fixture and connected the black wire from the two pin connector(fan) with the black wire from the 12-2. I connected the white wires from the two pin connector, three pin connector, and the 12-2 together. I connected the bare copper from the 12-2 to the green wire screwed to the fixture box.
That leaves the black wire (light) and red wire (night -light) still to be wired. I removed a black and a white wire from the yellow sheathing of some 12-2 NMB and stored away the bare copper wire. I then ran the black wire from the switch box to the black wire in the fixture (light) and connected them together. I took the white wire and ran it from the switch box to the red wire in the fixture (night-light). I got a red permanent marker and colored the white wire red at the switch box.
All the wire was ran through a gray PVC conduit.
I bought a double switch and a single switch for the light switches so that the fan can run off the single switch and the two lights will run off the double switch.
I have 5 wires sticking out of the metal switch box.
I have to come in from a power source somewhere. I would prefer another circuit for the bathroom but not sure if I have enough wire for it. I may have to temporarily drop down from the attic tying into some old Knob and Tube.
For some reason or other I am a bit confused about hooking up the switches. I have never hooked up a double switch and I wanna make sure I get this right. There are two black screws on one side of the switch, two copper on the other with a green screw in between the two copper. The other switch just has the two copper on one side with the green.
I assume the black wire from the light would hook to one black screw on the double switch while the white wire painted red (night-light) would hook to the other black screw on the double switch. I assume I would need to run the power source to the single switch then run a black wire from it to the double switch. Beyond these assumptions I am clueless and these assumptions may be clueless as well. Why this double switch is throwing me is driving me crazy.
Any help finishing this would be greatly appreciated.
Before anyone asks why I used 12-2.
I am going to eventually wire my whole house with it. It is all I have on hand. I can’t afford to go out and buy anything else right now and I want this bathroom light/fan/night-light working asap.
Thanks in advance for any help.
Background: Rick, a Homeowner from Pocahontas, AR
Additional Comments: Very nice website, if it helps me out with my projects I will gladly donate when I have the extra funds. Right now its really tough.
Thanks for your electrical question Rick.
I have provided the following links that lead to fully detailed information on this website that will assist you with your electrical question:
How to Install Bathroom Exhaust Fan Electrical Wiring
Bathroom Electrical Wiring
Fully Explained Photos and Wiring Diagrams for Bathroom Electrical Wiring with Code Requirements for most new or remodel projects.
For more information about Bath Exhaust Fan
Bath Exhaust Fan
This link is helpful as a Homeowner
Make sure not to miss these Resources for: How-To-Videos
Consult your Local Building Department about Permits and Inspections for all Electric Wiring Projects.
The Safest Way to Test Electrical Devices and Identify Electric Wires!The Non-Contact Electrical Tester
This is a testing tool that I have had in my personal electrical tool pouch for years, and is the first test tool I grab to help identify electrical wiring. It is a Non-contact tester that I use to easily Detect Voltage in Cables, Cords, Circuit Breakers, Lighting Fixtures, Switches, Outlets and Wires. Simply insert the end of the tester into an outlet, lamp socket, or hold the end of the tester against the wire you wish to test. Very handy and easy to use.
The Quickest Way to Check for Faulty Electrical Wiring!The Plug-In Outlet Tester
This is the first tool I grab to troubleshoot a problem with outlet circuit wiring. This popular tester is also used by most inspectors to test for power and check the polarity of circuit wiring.
It detects probable improper wiring conditions in standard 110-125 VAC outlets Provides 6 probable wiring conditions that are quick and easy to read for ultimate efficiency Lights indicate if wiring is correct and indicator light chart is included Tests standard 3-wire outlets UL Listed Light indicates if wiring is incorrect Very handy and easy to use.
Strip Off Wire Insulation without Nicking and Damaging the Electric Wire!The Wire Stripper and Wire Cutter
My absolute favorite wire stripping tool that I have had in my personal electrical tool pouch for years, and this is the tool I use to safely strip electrical wires.
This handy tool has multiple uses:
The wire gauges are shown on the side of the tool so you know which slot to use for stripping insulation.
The end of the tool can be used to grip and bend wire which is handy for attaching wire onto the screw terminals of switches and outlets..
The wire stripper will work on both solid and stranded wire. This tool is Very Handy and Easy to Use.
|More articles about Exhaust Fans and Home Electrical Wiring:|
|« Previous||Next »|
|Help for Ceiling Fan Wiring||How To Ground Old Two-Wire Outlets|